description: REPLANTEO Y NIVELACION (CON EQUIPO DE PRECISION) ALCANTARILLADO

description: ESTUDIOS DE LEVANTAMIENTO TOPOGRAFICO

description: SERVICIOS DE OBTENCION DE DATOS SOBRE LA CONFIGURACION, SITUACION Y/O DELIMITACION DE UNA PORCION DE LA SUPERFICIE TERRESTRE

description: ROTURA DE CARPE ASF.e=2" INCLUYE CORTADORA DE ASFALTO

description: SERVICIOS GENERALES DE CONSTRUCCION DE OBRAS NUEVAS

description: SERVICIOS GENERALES DE CONSTRUCCION (INCLUIDAS LAS OBRAS NUEVAS, AMPLIACIONES, REFORMAS Y RENOVACION)

description: EXCAVACION EN ZANJA A MAQUINA (SUELO SIN CLASIFICAR)

description: EXCAVACION DE ZANJAS

description: TRABAJOS DE EXCAVACION DE MOVIMIENTO DE TIERRAS, NIVELACION DE EMPLAZAMIENTOS DE OBRAS Y EXCAVACION DE ZANJAS

description: RELLENO COMPACTADO DE ZANJA EN CAPAS DE 20cm MAX

description: RELLENOS

description: TRABAJOS DE RELLENO Y DESMONTE, CON INCLUSION DE VOLADURAS, PERFORACIONES Y REMOCION DE ROCAS

description: S. C. BASE CLASE 1A

description: AGREGADOS PETREOS

description: CANTOS, GRAVA, PIEDRA PARTIDA O TRITURADA, DEL TIPO HABITUALMENTE UTILIZADO PARA HORMIGON ARMADO, AFIRMADO DE CARRETERAS O BALASTO PARA VIAS FERREAS U OTROS FINES, ASI COMO PEDERNALES Y GUIJARROS, TERMO TRATADOS O NO; MACADAN DE ESCORIA O DESECHOS INDUSTR

description: DESALOJO A MAQUINA (RETRO + VOLQUETA) HASTA 5km

description: VOLTEO (VOLQUETAS)

description: CAMIONES PARA APLICACIONES VARIAS

description: EXCAVACION PARA ESTRUCTURAS A MANO

description: EXCAVACION DE ZANJAS

description: REPOSIC. CARPETA ASF e=2" EN CALIENTE INC. IMPRIMAC

description: ASFALTADO DE VIAS SOBRE EMPEDRADO O BASE GRANULAR

description: SERVICIOS GENERALES DE CONSTRUCCION  EN CARRETERAS, CALLES, CAMINOS, OTRAS VIAS DE CIRCULACION  DE  VEHICULOS Y PEATONES, BARRERAS DE SEGURIDAD, VIAS FERREAS Y PISTAS DE ATERRIZAJE ETC.

description: EXCAVACION A MAQUINA SIN CLASIFICAR (ESTRUCTURAS)

description: EXCAVACION DE ZANJAS

description: LEVANTAMIENTO DE ADOQUIN Y APILADO

description: REPOSICION DE ADOQUIN CON EL MISMO MATERIAL

description: SOBREACARREO DE MATERIALES CON EQUIPO

description: VOLTEO (VOLQUETAS)

description: CAMIONES PARA APLICACIONES VARIAS

description: S. C. TUBERIA PVC DNI: 300mm ESTRUCTURADO INEN 2059, PRUEBA

description: TUBOS DE PVC

description: TUBOS, CANOS Y MANGUERAS RIGIDAS: MANGUERAS DE POLIMEROS DE ETILENO, PROPILENO, CLORURO DE VINILO, CANERIAS DE POLIMEROS DE ETILENO, RIGIDOS, DE FIBRA VULCANIZADA, ETC.

description: S. C. TUBERIA PVC DNI: 400mm ESTRUCTURADO INEN 2059, PRUEBA

description: TUBOS DE PVC

description: S. C. TUBERIA PVC DNI: 500mm ESTRUCTURADO INEN 2059, PRUEBA

description: TUBOS DE PVC

description: S. C. TUBERIA PVC DNI: 600mm ESTRUCTURADO INEN 2059, PRUEBA

description: TUBOS DE PVC

description: S. C. TUBERIA PVC DNI: 700mm ESTRUCTURADO INEN 2059, PRUEBA

description: TUBOS DE PVC

description: S. C. TUBERIA PVC DNI: 800mm ESTRUCTURADO INEN 2059, PRUEBA

description: TUBOS DE PVC

description: S. C. TUBERIA PVC DNI: 900mm ESTRUCTURADO INEN 2059, PRUEBA

description: TUBOS DE PVC

description: S. C. POZO REVISION h=0.80-2m f'c=180kg/cm2 Dint=0.9m PARED 20cm

description: CONSTRUCCION DE REDES URBANAS DE ALCANTARILLADO

description: SERVICIOS DE CONSTRUCCION CONDUCCIONES DE REDES URBANAS DE ABASTECIMIENTO DE AGUA  Y  ALCANTARILLADO  (INCLUIDAS LAS OBRAS AUXILIARES COMO ESTACIONES DE BOMBEO).

description: S. C. POZO REVISION h=2.01-3m f'c=180kg/cm2 Dint=0.9m PARED 20cm

description: S. C. TAPA H. N. INCLUIDO CERCO (40kn)

description: ALCANTARILLAS, REJILLAS, TAPAS DE ACERO O HIERRO REFRACTARIO

description: S. C. TUBERIA PVC DNI: 200mm ESTRUCTURADO INEN 2059, PRUEBA

description: TUBOS DE PVC

description: S. C. REJILLA H. N INC. CERCO

description: REJILLA DE HIERRO

description: OTRAS ESTRUCTURAS DE HIERRO Y ACERO (EXCEPTO EDIFICIOS PREFABRICADOS Y PARTES DE ESTRUCTURAS): CHAPAS, BARRAS, PERFILES, TUBOS, ANGULOS, BALAUSTRADAS, BALCONES, BARRERAS DE PASO A NIVEL, CERCAS, COMPONENTES DE EXCLUSAS, COMPUERTAS, ENREJADOS,ESCOTILLAS DE

description: TUBOS DE PVC

description: TUBOS DE PVC

description: S. C. POZO REVISION h=3.01-4m f'c=180kg/cm2 Dint=0.9m PARED 20cm

description: S. C. POZO REVISION h=4.01-5m f'c=210kg/cm2 Dint=1.2m PARED 30cm

description: S. C. TUBERIA PVC DNI: 160mm ESTRUCTURADO INEN 2059, PRUEBA

description: TUBOS DE PVC

description: S. C. SILLA ADAPTADORA 250mmX160mm

description: TUBOS DE PVC

description: CAJA DOMICILIARIA 0.60X0.60 h=1.00m. H. S. f'c=180 kg/cm2 INC. TAPA H. A. E=7cm

description: ARGAMASAS Y HORMIGON NO REFRACTARIOS

description: ARGAMASAS Y HORMIGON NO REFRACTARIOS

description: S. C. TUBERIA PVC DNI: 250mm ESTRUCTURADO INEN 2059, PRUEBA

description: TUBOS DE PVC

description: HORMIGÓN SIMPLE f'c=180 kg/cm2

description: HORMIGON PREMEZCLADO

description: HORMIGON

description: HORMIGON SIMPLE f'c=210 kg/cm2

description: HORMIGON PREMEZCLADO

description: HORMIGON

description: S. C. JUNTA PVC 18cm

description: TUBOS DE PVC

description: S. C. ENCOFRADO Y DESENCOFRADO METALICO CIRCULAR Y/O RECTO

description: S. C. ACERO DE REFUERZO fy=4200 kg/cm2

description: VARILLAS DE HIERRO PARA LA CONSTRUCCION

description: ESTRUCTURAS DE HIERRO Y ACERO: PUNTALES Y EQUIPO ANALOGO PARA ANDAMIAJES, ENCOFRADOS O APUNTALAMIENTO DE POZOS DE MINAS: ANDAMIAJES TUBULARES, MARCOS DE BOCAMINA, PUNTALES AJUSTABLES O TELESCOPICOS, ETC.

description: S. C. ENTIBADO ZANJA

description: S. C. MURO GAVIÓN TRIPLE TORSIÓN

description: GAVION DE ALAMBRE DE ACERO GALVANIZADO

description: GAVIONES

description: SUMINISTRO DE AGUA EN TANQUEROS

description: S. C. LETRERO DE SEÑALIZACION (A=1.20 H=0.70)

description: POR CUMPLIR CON TODO LO SOLICITADO EN LOS PLIEGOS

description: REPLANTEO Y NIVELACION CON EQUIPO DE PRECISION ALCANTARILLADO

description: ESTUDIOS DE LEVANTAMIENTO TOPOGRAFICO

description: SERVICIOS DE OBTENCION DE DATOS SOBRE LA CONFIGURACION, SITUACION Y/O DELIMITACION DE UNA PORCION DE LA SUPERFICIE TERRESTRE

description: ROTURA DE CARPE ASF.e=2- INCLUYE CORTADORA DE ASFALTO

description: SERVICIOS GENERALES DE CONSTRUCCION DE OBRAS NUEVAS

description: SERVICIOS GENERALES DE CONSTRUCCION (INCLUIDAS LAS OBRAS NUEVAS, AMPLIACIONES, REFORMAS Y RENOVACION)

description: EXCAVACION EN ZANJA A MAQUINA SUELO SIN CLASIFICAR

description: EXCAVACION DE ZANJAS

description: TRABAJOS DE EXCAVACION DE MOVIMIENTO DE TIERRAS, NIVELACION DE EMPLAZAMIENTOS DE OBRAS Y EXCAVACION DE ZANJAS

description: RELLENO COMPACTADO DE ZANJA EN CAPAS DE 20cm MAX

description: RELLENOS

description: TRABAJOS DE RELLENO Y DESMONTE, CON INCLUSION DE VOLADURAS, PERFORACIONES Y REMOCION DE ROCAS

description: S. C. BASE CLASE 1A

description: AGREGADOS PETREOS

description: DESALOJO A MAQUINA RETRO + VOLQUETA HASTA 5km

description: VOLTEO (VOLQUETAS)

description: CAMIONES PARA APLICACIONES VARIAS

description: EXCAVACION PARA ESTRUCTURAS A MANO

description: EXCAVACION DE ZANJAS

description: TRABAJOS DE EXCAVACION DE MOVIMIENTO DE TIERRAS, NIVELACION DE EMPLAZAMIENTOS DE OBRAS Y EXCAVACION DE ZANJAS

description: REPOSIC. CARPETA ASF e=2- EN CALIENTE INC. IMPRIMAC

description: ASFALTADO DE VIAS SOBRE EMPEDRADO O BASE GRANULAR

description: EXCAVACION A MAQUINA SIN CLASIFICAR ESTRUCTURAS

description: EXCAVACION DE ZANJAS

description: TRABAJOS DE EXCAVACION DE MOVIMIENTO DE TIERRAS, NIVELACION DE EMPLAZAMIENTOS DE OBRAS Y EXCAVACION DE ZANJAS

description: LEVANTAMIENTO DE ADOQUIN Y APILADO

description: ADOQUINES EXAGONALES DE CONCRETO  300 KG/CM2M2 DE RESISITENCIA

description: BALDOSAS Y LOSAS PARA PAVIMENTOS, CHIMENEAS Y MUROS, SIN ESMALTAR:  ADOQUINES DE BARRO COMUN, LOSAS DE BARRO COMUN, DE CERAMICA SIN VIDRIAR, ETC.

description: REPOSICION DE ADOQUIN CON EL MISMO MATERIAL

description: ADOQUINES EXAGONALES DE CONCRETO  300 KG/CM2M2 DE RESISITENCIA

description: BALDOSAS Y LOSAS PARA PAVIMENTOS, CHIMENEAS Y MUROS, SIN ESMALTAR:  ADOQUINES DE BARRO COMUN, LOSAS DE BARRO COMUN, DE CERAMICA SIN VIDRIAR, ETC.

description: SOBREACARREO DE MATERIALES CON EQUIPO

description: VOLTEO (VOLQUETAS)

description: CAMIONES PARA APLICACIONES VARIAS

description: S. C. TUBERIA PVC DNI: 300mm ESTRUCTURADO INEN 2059, PRUEBA

description: TUBOS DE PVC

description: S. C. TUBERIA PVC DNI: 400mm ESTRUCTURADO INEN 2059, PRUEBA

description: TUBOS DE PVC

description: S. C. TUBERIA PVC DNI: 500mm ESTRUCTURADO INEN 2059, PRUEBA

description: TUBOS DE PVC

description: S. C. TUBERIA PVC DNI: 600mm ESTRUCTURADO INEN 2059, PRUEBA

description: TUBOS DE PVC

description: S. C. TUBERIA PVC DNI: 700mm ESTRUCTURADO INEN 2059, PRUEBA

description: TUBOS DE PVC

description: S. C. TUBERIA PVC DNI: 800mm ESTRUCTURADO INEN 2059, PRUEBA

description: TUBOS DE PVC

description: S. C. TUBERIA PVC DNI: 900mm ESTRUCTURADO INEN 2059, PRUEBA

description: TUBOS DE PVC

description: S. C. POZO REVISION h=0.80-2m f-c=180kg/cm2 Dint=0.9m PARED 20cm

description: CONSTRUCCION DE REDES URBANAS DE ALCANTARILLADO

description: S. C. POZO REVISION h=2.01-3m f-c=180kg/cm2 Dint=0.9m PARED 20cm

description: CONSTRUCCION DE REDES URBANAS DE ALCANTARILLADO

description: S. C. TAPA H. N. INCLUIDO CERCO 40kn

description: ALCANTARILLAS, REJILLAS, TAPAS DE ACERO O HIERRO REFRACTARIO

description: S. C. TUBERIA PVC DNI: 200mm ESTRUCTURADO INEN 2059, PRUEBA

description: TUBOS DE PVC

description: S. C. REJILLA H. N INC. CERCO

description: REJILLA DE HIERRO

description: S. C. TUBERIA PVC DNI: 300mm ESTRUCTURADO INEN 2059, PRUEBA

description: TUBOS DE PVC

description: S. C. TUBERIA PVC DNI: 400mm ESTRUCTURADO INEN 2059, PRUEBA

description: TUBOS DE PVC

description: S. C. POZO REVISION h=0.80-2m f-c=180kg/cm2 Dint=0.9m PARED 20cm

description: CONSTRUCCION DE REDES URBANAS DE ALCANTARILLADO

description: S. C. POZO REVISION h=2.01-3m f-c=180kg/cm2 Dint=0.9m PARED 20cm

description: CONSTRUCCION DE REDES URBANAS DE ALCANTARILLADO

description: S. C. POZO REVISION h=3.01-4m f-c=180kg/cm2 Dint=0.9m PARED 20cm

description: CONSTRUCCION DE REDES URBANAS DE ALCANTARILLADO

description: S. C. POZO REVISION h=4.01-5m f-c=210kg/cm2 Dint=1.2m PARED 30cm

description: CONSTRUCCION DE REDES URBANAS DE ALCANTARILLADO

description: S. C. TUBERIA PVC DNI: 160mm ESTRUCTURADO INEN 2059, PRUEBA

description: TUBOS DE PVC

description: S. C. SILLA ADAPTADORA 250mmX160mm

description: TUBOS DE PVC

description: CAJA DOMICILIARIA 0.60X0.60 h=1.00m. H. S. f-c=180 kg/cm2 INC. TAPA H. A. E=7cm

description: ARGAMASAS Y HORMIGON NO REFRACTARIOS

description: ARGAMASAS Y HORMIGON NO REFRACTARIOS

description: S. C. TUBERIA PVC DNI: 250mm ESTRUCTURADO INEN 2059, PRUEBA

description: TUBOS DE PVC

description: HORMIGÓN SIMPLE f-c=180 kg/cm2

description: HORMIGON PREMEZCLADO

description: HORMIGON

description: HORMIGON SIMPLE f-c=210 kg/cm2

description: HORMIGON PREMEZCLADO

description: HORMIGON

description: S. C. JUNTA PVC 18cm

description: TUBOS DE PVC

description: S. C. ENCOFRADO Y DESENCOFRADO METALICO CIRCULAR Y/O RECTO

description: SERVICIOS GENERALES DE CONSTRUCCION DE OBRAS NUEVAS

description: SERVICIOS GENERALES DE CONSTRUCCION (INCLUIDAS LAS OBRAS NUEVAS, AMPLIACIONES, REFORMAS Y RENOVACION)

description: S. C. ACERO DE REFUERZO fy=4200 kg/cm2

description: VARILLAS DE HIERRO PARA LA CONSTRUCCION

description: S. C. ENTIBADO ZANJA

description: SERVICIOS GENERALES DE CONSTRUCCION DE OBRAS NUEVAS

description: SERVICIOS GENERALES DE CONSTRUCCION (INCLUIDAS LAS OBRAS NUEVAS, AMPLIACIONES, REFORMAS Y RENOVACION)

description: S. C. MURO GAVIÓN TRIPLE TORSIÓN

description: GAVION DE ALAMBRE DE ACERO GALVANIZADO

description: GAVIONES

description: S. C. PUENTE PEATONAL MADERA PROVISIONAL

description: SERVICIOS GENERALES DE CONSTRUCCION DE PUENTES, PEATONES Y FERROCARRILES, ETC.

description: SERVICIOS GENERALES DE CONSTRUCCION DE PUENTES, CARRETERAS ELEVADAS, VIADUCTOS, TUNELES Y SUBTERRANEOS PARA CIRCULACION DE VEHICULOS, PEATONES Y FERROCARRILES, ETC.

description: CONTROL DE POLVO EN ZANJA TANQUERO 6m3

description: SUMINISTRO DE AGUA EN TANQUEROS

description: TRANSPORTE POR CARRETERA DE OTROS GASES O LIQUIDOS A GRANEL EN CAMIONES CISTERNA ESPECIALES

description: S. C. LETRERO DE SEÑALIZACION A=1.20 H=0.70

description: CONFECCION DE VALLAS PUBLICITARIAS, INCLUYE ROTULOS, VALLAS, GIGANTOGRAFIAS, ETC

description: CONFECCION DE VALLAS PUBLICITARIAS, INCLUYE ROTULOS, VALLAS, GIGANTOGRAFIAS, ETC

title: LICO-EPEMAPAA-02-20-545597

answer: Estimado oferente, favor sujétese a los pliegos específicamente a la observación 1. Además sujétese a la ACLARACION 1 Y ACLARACION 2.

description: Buenos díasLA oferta podrá ser enviada mediante correo electrónico al correo de la institución mediante al plataforma WETRANSFER de acuerdo a la resolución del sercop por el estado de emergencia por el COVID-19?

answer: Respuesta 2.- Si, estimado oferente, favor sujétese a los pliegos y al ANEXO EXPERIENCIA GENERAL Y ESPECÍFICA MÍNIMA. Además sujétese a la ACLARACION 1 Y ACLARACION 2.

description: Señores EP-EMAPA-A, buen día. Será válida para la experiencia específica la construcción de colectores de hormigón armado para alcantarillado?

answer: Respuesta 3.-Si, estimado oferente, favor sujétese a los pliegos y al ANEXO EXPERIENCIA GENERAL Y ESPECÍFICA MÍNIMA. Además sujétese a la ACLARACION 1 Y ACLARACION 2.

description: Será válida para la experiencia específica la construcción de colectores de alcantarillado con tubería PVC de pared estructurada de diámetros iguales o superiores a 900mm?

answer: Respuesta 4.-Estimado oferente, LA EXPERIENCIA DEL OFERENTE será evaluada en la evaluación cumple no cumple, conforme a lo indicado en el ANEXO EXPERIENCIA GENERAL Y ESPECIFICA MINIMA,  por puntaje se evaluará conforme a lo indicado en el pliego en el numeral 4.2 EVALUACION POR PUNTAJE.LA EXPERIENCIA DEL  PERSONAL TÉCNICO será evaluada por puntaje conforme a lo indicado en el pliego en el numeral 4.2 EVALUACION POR PUNTAJE. Los archivos se encuentran debidamente publicados en el Portal de Compras Públicas. Además sujétese a la ACLARACION 1 Y ACLARACION 2.

name: NOBELCONS NOBEL CONSTRUCCIONES CIA. LTDA.

description: BUENAS TARDES POR FAVOR PUEDEN SUBIR EL ARCHIVO DONDE INDIQUE COMO SE EVALUARA LA EXPERIENCIA DEL OFERENTE Y DEL PERSONAL TÉCNICO GRACIAS

answer: Respuesta 5.-NO, Estimado Oferente favor sujétese a los pliegos y al ANEXO EXPERIENCIA GENERAL Y ESPECIFICA MINIMA. Además sujétese a la ACLARACION 1 Y ACLARACION 2.

description: buenas tardes estoy ejecutando un proyecto y estamos en un avance del 75% para ser oferente puedo presentar el certificado de la fiscalización conjuntamente con el contrato y la planilla ejecutada o indicar cuales son los requerimientos para poder participar.

answer: Respuesta 6.-Estimado oferente las cantidades consideradas en el rubro excavación obedecen a un estudio previo,  favor sujétese a los pliegos. Además sujétese a la ACLARACION 1 Y ACLARACION 2.

description: En el Rubro excavacion no se especifica las diferentes alturas que se tiene en la construccion del alcantarillado en base de que altura tiene el precio referencial, es responzabilidad de la Entidad entregar los rubros a construir a detalle para poder ofertar

answer: Respuesta 7.-Estimado oferente, las tapas son de Hierro Nodular  H.N.. Favor sujétese a los pliegos,  al ANEXO ESPECIFICACIONES TECNICAS PAGINA 68.  Además sujétese a la ACLARACION 1 Y ACLARACION 2.

description: Las tapas S. C. TAPA H. N. INCLUIDO CERCO 40kn de los pozos es de HD o HF? las especificaciones no son claras bajo cual es la norma de las tapas.

answer: Respuesta 8.-Si, estimado oferente, favor sujétese a los pliegos al ANEXO EXPERIENCIA GENERAL Y ESPECÍFICA MÍNIMA.  Además sujétese a la ACLARACION 1 Y ACLARACION 2.

description: SEÑORES, LA OBRA DESCARGA DE AGUA PLUVIAL CON TUB PVC D=540 MM APLICA COMO EXPERIENCIA ESPECIFICA?

answer: Respuesta 9.-Si, estimado oferente, favor sujétese a los pliegos al ANEXO EXPERIENCIA GENERAL Y ESPECÍFICA MÍNIMA. Además sujétese a la ACLARACION 1 Y ACLARACION 2.

description: Se puede cumplir experiencia general y específica, con la suma de varios contratos?

answer: Respuesta 10.-Si, estimado oferente, favor sujétese a los pliegos, al ANEXO EXPERIENCIA GENERAL Y ESPECÍFICA MÍNIMA. Además sujétese a la ACLARACION 1 Y ACLARACION 2.

description: Se puede cumplir experiencia general y específica, con la suma de varios contratos?

answer: Respuesta 11.-Si, estimado oferente, favor sujétese a los pliegos,  al ANEXO EXPERIENCIA GENERAL Y ESPECÍFICA MÍNIMA.  Además sujétese a la ACLARACION 1 Y ACLARACION 2.

description: Estimada comisión favor indicar si se aceptará la experiencia en construcción de colectores de hormigón? Gracias

answer: Respuesta 12.-Si, Estimado Oferente siempre y cuando en el Acta de Entrega Recepción estén definidos y separados los rubros de Alcantarillado de los de Agua Potable, mediante títulos y cumplan con las condiciones establecidas en los pliegos,  favor sujétese a los pliegos. Además sujétese a la ACLARACION 1 Y ACLARACION 2.

description: Estimada entidad contratante, para el presente proceso se acepta la construcción de obras que tienen por objeto agua potable y alcantarillado en el mismo contrato? Favor indicar si es factible o no, gracias.

answer: Respuesta 13.-No, estimado oferente, favor sujétese a los pliegos. Además sujétese a la ACLARACION 1 Y ACLARACION 2.

description: BUENAS TARDES EN EL EQUIPO MINIMO SOLICITAN UNA CARGADORA FRONTAL ES FACTIBLE REEMPLAZARLA POR UNA MINICARGADORA YA QUE LA CAPACIDAD QUE ESTÁN SOLICITANDO ESTÁ EN UN RANGO MUY BAJO  PARA CARGADORA FRONTAL

answer: Respuesta 14.-Estimado oferente, favor sujétese a los pliegos. Además sujétese a la ACLARACION 1 Y ACLARACION 2.

description: BUENAS TARDES POR FAVOR SOLICITO COLOQUEN CUAL ES LA POTENCIA EN HP DEL RODILLO VIBRATORIO REQUERIDO EN LA OFERTA GRACIAS

answer: Respuesta 15Estimado oferente para estas profundidades en los volúmenes de obra está considerado realizar plataformas para alcanzar las profundidades solicitadas, y se ha considerado entibado de zanja, estas consideraciones para el tramo en el que se requiere estas profundidades.  Además sujétese a la ACLARACION 1 Y ACLARACION 2.

description: SALUDOS, QUISIERA SABER SI EXISTE ALGUN ESTUDIO GEOLOGICO O GEOTECNICO QUE AVALE LA ESTABILIDAD DEL TERRENO PARA  PODER HACER EXCAVACIONES TAN PROFUNDAS DE HASTA 11 METROS, YA QUE SI NO SE TIENE UN SUELO ESTABLE O SE TIENE  PRESENCIA DE AGUA , UN SISTEMA DE ENTIBADO COMUN PONDRA EN RIESGO LA INTEGRIDAD DE LAS PERSONAS QUE TRABAJARAN DENTRO DE LA ZANJA.  FAVOR ACLARAR ESTO O EN SU DEFECTO MODIFICAR EL DISEÑO PARA OBTENER PROFUNDIDADES MENORES.

answer: Respuesta 16.-Estimado oferente los pozos hasta 5 metros son de hormigón simple, los pozos de 6 a 8 metros son de hormigón armado y para las alturas de 8 metros en adelante son cajas especiales, lo que gráficamente se indica en los planos, favor sujétese a los pliegos. Además sujétese a la ACLARACION 1 Y ACLARACION 2.

description: Señores EP-EMAPA-A, por favor aclarar la siguiente duda: Cuál es el diseño que se utilizará para los pozos de altura mayor a 6 m, el que consta en la lámina 7/10 o el que consta en la lámina de detalles de pozos. Por favor aclarar según la altura del pozo, pues tenemos pozos de hasta 11 metros.

answer: Respuesta 17.-Si estimado Oferente se dará estricto cumplimiento a lo indicado en la Normativa y a lo indicado en los pliegos. Además sujétese a la ACLARACION 1 Y ACLARACION 2.

description: DE ACUERDO A LOS PLIEGOS Los requisitos mínimos: EQUIPO MÍNIMO, PERSONAL TÉCNICOMÍNIMO, EXPERIENCIA MÍNIMA DEL PERSONAL TÉCNICO, Y METODOLOGÍA DE EJECUCIÓN DELPROYECTO, conforme lo establecido por el SERCOP según Resoluciones No. R.E.-SERCOP-2019-000095 yRE-SERCOP-2019-0000100 de 07 de enero y 04 de julio de 2019, respectivamente, no serán consideradoscomo requisitos mínimos de la oferta, ni serán objeto de evaluación por puntaje. 4. El cumplimiento de losrequisitos mínimos detallados en el acápite precedente, se considerará cumplido con la sola presentacióny verificación de la suscripción del ?II. FORMULARIO DE COMPROMISO DE CUMPLIMIENTO DEPARÁMETROS EN ETAPA CONTRACTUAL, SE CUMPLIRA CON LA RESOLUCION SI O NO, GRACIAS

answer: Respuesta 18.-Si estimado Oferente por favor remítase a lo indicado en los pliegos y en el ANEXO EXPERIENCIA GENERAL Y ESPECIFICA MINIMA en donde claramente se señala mínimo 1 proyecto, es decir puede presentar uno o más proyectos, siempre y cuando cumpla con los requerimientos solicitados. Además sujétese a la ACLARACION 1 Y ACLARACION 2.

description: PARA CUMPLIR CON LA ESPERIENCIA TANTO GENERAL Y ESPECIFICA SE PUEDE PRESENTAR UN SIN NUMERO DE OBRAS HASTA LLEGAR A CUMPLIR CON EL PRESUPESTO REFERENCIAL?

answer: Respuesta 19.-Estimado oferente el pozo que usted señala no requiere salto de desvió, ya que por su profundidad se considera como caja especial por favor sujétese a los pliegos. Además sujétese a la ACLARACION 1 Y ACLARACION 2.

description: Por favor aclarar cómo se cancelará el rubro "salto de desvío de pozos de revisión", tanto en pozos de hasta 4m, como en pozos de más de 4m. Además por favor subir el detalle del salto de desvío del Pozo-58 alcantarillado pluvial cuya altura es de 9.61 metros, pues por la altura debería considerarse un pozo de bandejas o similar y si es así por favor subir el diseño del mismo.

answer: Respuesta 20.-Si, estimado oferente se dará estricto cumplimiento a la Normativa vigente, favor sujétese a los pliegos. Además sujétese a la ACLARACION 1 Y ACLARACION 2.

description: Estimados, de acuerdo a la normativa vigente, LOSNCP Art. 99 se va a aceptar el 100% del monto ejecutado de una obra que se haya realizado en consorcio, independientemente de su participación, al igual que en el proceso anterior.  Saludos.

answer: Respuesta 21.-Estimado Oferente favor remitirse a los pliegos, el administrador del contrato conjuntamente con el fiscalizador solicitaran este requerimiento al contratista al inicio de la ejecución contractual. Además sujétese a la ACLARACION 1 Y ACLARACION 2.

description: Pregunta, en la oferta en el formulario 1.10. PERSONAL TÉCNICO PROPUESTO PARA EL PROYECTO, deberíamos enlistar al personal técnico, más si cumple o no con la solicitud de los pliegos no será causal de rechazo, ya que este parámetro se considerará Conforme lo establecido por el SERCOP según Resoluciones No. R.E.-SERCOP-2019-000095 y RE-SERCOP-2019-0000100 de 07 de enero y 04 de julio de 2019, respectivamente, no serán considerados como requisitos mínimos de la oferta, ni serán objeto de evaluación por puntaje. Tomando en cuenta que en el momento de la ejecución de la obra ya deberíamos presentar al personal técnico solicitado.  O SERÍA MEJOR, apegándonos a las reformas a la norma, REEMPLAZAR el formulario 1.10 y el Formulario II, donde consta Compromiso y Hoja de vida del personal técnico, POR EL FORMULARIO DE COMPROMISO DE CUMPLIMIENTO. Gracias

answer: Respuesta 22.-Estimado oferente la forma de evaluación está claramente definida en los pliegos en la Observación 3,  favor remitirse a los pliegos. Además sujétese a la ACLARACION 1 Y ACLARACION 2.

description: Solicito una aclaración en cuanto a la sección EVALUACION DE LA OFERTA ECONOMICA,  Tomando en cuenta que la entidad subirá los análisis y los oferentes realícenlos APU?s en base a éstos, y podremos acogemos y replicar o hacer en base a estos análisis, se entendería que no debería haber errores de precios unitarios y por lo tanto el puntaje de todos los oferentes, que se basan en los precios unitarios de la entidad,  deberían ser el máximo y no variar por supuestos errores en los precios unitarios ya que están basados en los que la entidad contratante emite. Menciono esto en razón que en algunas instituciones no confiables utilizan cualquier tipo de artimaña para eliminar ofertas basándose en los análisis de precios unitarios y diciendo que no se encuentran bien realizados, pese a que ellos suben de igual manera los análisis de precios. Ustedes saben como profesionales, que la ejecución de análisis de precios unitarios es muy variable y dependen mucho del criterio del que los realiza.

answer: Respuesta 23.-Estimado Oferente siempre y cuando en el Acta de Entrega Recepción estén definidos y separados los rubros de Alcantarillado, mediante títulos y cumplan con las condiciones establecidas en los pliegos, favor remitirse a los pliegos. Además sujétese a la ACLARACION 1 Y ACLARACION 2.

description: Tengo experiencia en una obra denominada INFRSESTRUCTURA VIAL Y SANITARIA DE ", sirve como experiencia especifica? Responder si o no, gracias

answer: Respuesta 24.-Estimado Oferente siempre y cuando en el Acta de Entrega Recepción estén definidos y separados los rubros de Alcantarillado, mediante títulos y cumplan con las condiciones establecidas en los pliegos, favor remitirse a los pliegos. Además sujétese a la ACLARACION 1 Y ACLARACION 2.

description: MUY BUENAS UNA CONSULTA OBRA DE CONEXIONES DOMICILIARIAS EN LA CUAL EXISTEN RUBROS DE ALCANTARILLADO SE ACEPTARA COMO EXPERIENCIA ESPECIFICA Y GENERAL

answer: Respuesta 25.-Estimado Oferente si se aceptara el 100%, favor sujétese a los pliegos. Además sujétese a la ACLARACION 1 Y ACLARACION 2.

description: SEÑORES ENTIDAD CONTRATANTE LA EXPERIENCIA ADQUIRIDA EN COMO CONSORCIO,  LA EXPERIENCIA  DE UN SOCIO SERA TOMADO EL VALOR TOTAL  DEL CONTRATO O ÚNICAMENTE EL PORCENTAJE DE PARTICIPACIÓN DE CADA CONSORCIADO?

answer: Respuesta 26No, estimado oferente, favor sujétese a los pliegos al ANEXO EXPERIENCIA GENERAL Y ESPECÍFICA MÍNIMA.  Además sujétese a la ACLARACION 1 Y ACLARACION 2.

description: ESTIMADOS SEÑORES DEL GAD, LA PRESENTE TIENE POR OBJETO SOLICITAR QUE SE CONSIDERE VALIDAREXPERIENCIA GENERAL-ESPECIFICA EN SISTEMAS DE AGUA POTABLE, YA QUE LOS TRABAJOS SON MUY SIMILARES, YCON ESTO SE PUEDE TENER MAYOR CONCURRENCIA E IGUALDAD DE OPORTUNIDADES SEGÚN LOS PRINCIPIOS QUERIGEN LA CONSTITUCIÓN DE LA REPÚBLICA, SITUACIÓN QUE BENEFICIA A LA ENTIDAD EN TODO ASPECTO.ADICIONAL MENTE TOMEN EN CUENTA QUE EXISTIMOS MUCHOS PROFESIONALES QUE ESTAMOS SIN TRABAJOS VARIOSMESES. GRACIAS

answer: Respuesta 27.-Si, estimado oferente, favor sujétese a los pliegos,  al ANEXO EXPERIENCIA GENERAL Y ESPECÍFICA MÍNIMA.  Además sujétese a la ACLARACION 1 Y ACLARACION 2.

description: saludos señores colectores de hormigon armado puede considerarse como experiencia especifica

answer: Respuesta 28Estimado oferente la comisión revisara y analizara que realicen la correcta estructuración del Análisis de Precios Unitarios, especialmente en el cumplimiento de: equipo, mano de obra, materiales, y cantidades mínimas solicitados por la EP-EMAPA-A, además de rendimientos reales que estén acorde con los componentes de los APUS presentados por el oferente, de tal forma que permita dar estricto cumplimiento con las Especificaciones Técnicas. Además sujétese a la ACLARACION 1 Y ACLARACION 2.

description: señres por favor indicar en que porcentaje se puede subir o bajar los rendimientos en los rubros para que no sean motivo de descalificacion ya que el parametro es muy subjetivo, por favor la respuesta numerica y que no sean remitidos a pliegos

answer: Respuesta 29.-Estimado Oferente si se aceptara el 100%, favor sujétese a los pliegos. Además sujétese a la ACLARACION 1 Y ACLARACION 2.

description: ESTIMADOS  EP-EMAPA-A, EN CASO DE TENER EXPERIENCIA ESPECÍFICA O GENERAL DENTRO DE UN CONSORCIO, EL PORCENTAJE PARA LOS SOCIOS DE ACUERDO AL MONTO DEL CONTRATO, SERÁ EL 100% O SERÁ EL PORCENTAJE ESTABLECIDO PARA CADA SOCIO DE ACUERDO A LO ESTIPULADO EN LA CONFORMACIÓN DEL MISMO?

answer: Respuesta 30.-Estimado Oferente si se aceptara como Fiscalizador de Obra. Conforme lo indica claramente en el ANEXO EXPERIENCIA GENERAL Y ESPECÍFICA MÍNIMA,  favor sujétese a los pliegos. Además sujétese a la ACLARACION 1 Y ACLARACION 2.

description: El oferente puede presentar como experiencia general en calidad de fiscalizador? sin tener que estar bajo relación de dependencia, sino directamente como contratista fiscalizador..?

answer: Respuesta 31Estimado oferente para estas profundidades en los volúmenes de obra está considerado realizar plataformas para alcanzar las profundidades solicitadas, y se ha considerado entibado de zanja, estas consideraciones para el tramo en el que se requiere estas profundidades.  Además sujétese a la ACLARACION 1 Y ACLARACION 2.

description: Buenas tardes Señores de la Comisión Técnica, de los planos del Proyecto se determina que deberán realizarse excavaciones hasta de 11 metros de profundidad equivalente a un edificio de 4 pisos, por lo cual es indispensable que nos remitan los Estudios de Suelos, para poder determinar los sistemas a utilizar en la excavación, esto es secciones de excavación, entibamiento  etc., como también conocer la presencia de agua en dichas excavaciones.

answer: Respuesta 32.-Estimado Oferente no se aceptara. Favor sujétese a los pliegos al ANEXO EXPERIENCIA GENERAL Y ESPECÍFICA MÍNIMA.  Además sujétese a la ACLARACION 1 Y ACLARACION 2.

description: Buenas noches disculpen el proyecto que se esta ejecutando es una planta de tratamiento dentro de los rubros existen alcantarillados mas de 1 millon de dolares sera aceptado

answer: Respuesta 33.-Estimado Oferente se aceptara el 40% del monto del total de la obra para Fiscalizador de Obra, para residente de fiscalización no se aceptará.  Favor sujétese a los pliegos,  al ANEXO EXPERIENCIA GENERAL Y ESPECÍFICA MÍNIMA.  Además sujétese a la ACLARACION 1 Y ACLARACION 2.

description: Buenas noches, favor indicar si la experiencia en calidad de fiscalización o residente de fiscalización es válida para experiencia general y cuál es el monto válido el de obra o el monto del contrato de fiscalización

answer: Respuesta 34.-Estimado Oferente si con la presentación de un instrumento que acredite la experiencia mínima específica, el proveedor cumpliere el monto mínimo solicitado para la experiencia mínima general, este instrumento será considerado como válido para acreditar los dos tipos de experiencias. No se aceptara como residente de fiscalización. Favor sujétese a los pliegos al ANEXO EXPERIENCIA MINIMA PERSONAL TECNICO RESIDENTES DE OBRA. Además sujétese a la ACLARACION 1 Y ACLARACION 2.

description: Favor indicar si el monto de la experiencia específica sobrepasa elValor mínimo el excedente se validará como experiencia general o el monto total será validado también para la general.También aclara si la experiencia como residente de Fiscalización es válida para residente de obra y superintendente

answer: Respuesta 35.-La EP-EMAPA-A, no publica este documento en el portal de Compras Públicas por cuanto como usted indica son de dominio público y se encuentran publicados y disponibles en el portal del INEN y son los documentos actualizados. Es importante indicar que la EP-EMAPA-A se sujeta al Código Ecuatoriano Construcción de obras Sanitarias Norma CO 10.07-601, CO 10.07-602, Normas del ex IEOS donde la subsecretaria del Agua Potable y Saneamiento Básico solicita obligatoriamente utilizar las normas para las fichas ambientales además en las especificaciones técnicas se hace constar las normas GE-500-7-150 – 1083, ACI, ASTEM, AASHTO y las normas INEN. Favor sujétese a los pliegos. Además sujétese a la ACLARACION 1 Y ACLARACION 2.

description: Los Reglamentos Técnicos Ecuatorianos RTE-INEN son dedominio y uso público y se encuentran publicados y disponibles en el portal del INEN. Petitorio: favor incluir en el presente proceso de compras públicas.

answer: Respuesta 36.-La EP-EMAPA-A, no publica este documento en el portal de Compras Públicas por cuanto como usted indica son de dominio público y se encuentran publicados y disponibles en el portal del INEN y son los documentos actualizados. Es importante indicar que la EP-EMAPA-A se sujeta al Código Ecuatoriano Construcción de obras Sanitarias Norma CO 10.07-601, CO 10.07-602, Normas del ex IEOS donde la subsecretaria del Agua Potable y Saneamiento Básico solicita obligatoriamente utilizar las normas para las fichas ambientales además en las especificaciones técnicas se hace constar las normas GE-500-7-150 – 1083, ACI, ASTEM, AASHTO y las normas INEN. Favor sujétese a los pliegos. Además sujétese a la ACLARACION 1 Y ACLARACION 2.

description: Adicionalmente el Ecuador cuenta con la Norma Técnica Ecuatoriana NTE-INEN-EN-124:2019 Tapas dePozos y rejillas y, los anexos correspondientes a diversos materiales: Hierro Nodular, Hierro Gris,Acero, Hormigón, Plásticos, entre otros. Petitorio: solicitamos de la manera más comedida incluircomo parte de los pliegos la norma Técnica Ecuatoriana: NTE-INEN-EN-124:2019 vigente.

answer: Respuesta 37.-La EP-EMAPA-A, no publica este documento en el portal de Compras Públicas por cuanto como usted indica son de dominio público y se encuentran publicados y disponibles en el portal del INEN y son los documentos actualizados. Es importante indicar que la EP-EMAPA-A se sujeta al Código Ecuatoriano Construcción de obras Sanitarias Norma CO 10.07-601, CO 10.07-602, Normas del ex IEOS donde la subsecretaria del Agua Potable y Saneamiento Básico solicita obligatoriamente utilizar las normas para las fichas ambientales además en las especificaciones técnicas se hace constar las normas GE-500-7-150 – 1083, ACI, ASTEM, AASHTO y las normas INEN. Favor sujétese a los pliegos. Además sujétese a la ACLARACION 1 Y ACLARACION 2.

description: El presente proceso LICO-EPEMAPAA-02-20 incluye diversos tipo de tapas de pozos y rejillasfabricadas en diversos materiales designados como TAPA DE ESTRUCTURA METALICAL, HF, HA, HD estos términos técnicos aplicados en el pliego no corresponden a los nombres técnicos de los materiales definidos en la normativas técnicas ecuatorianas actualmente vigentes. Petitorio: solicitamos de la manera más comedida se incluya como parte de los pliegos las especificaciones técnicas de las Tapas de Pozos y Rejillas así como de los materiales a ser utilizados para la fabricación de  dichos bienes acordes con las Normas Técnicas Ecuatorianas: NTE-INEN-EN-124:2019, NTE-INEN-2496, EN-INEN-2499 vigentes.

answer: Respuesta 38.-Estimado Oferente favor remitirse a los pliegos.  Además sujétese a la ACLARACION 1 Y ACLARACION 2.

description: La evidenciación de conformidad de las Tapas de Pozos y Rejillas se encuentran detalladas en elReglamento Técnico Ecuatoriano RTE-INEN-062 de carácter obligatorio numeral, 7 Ensayos paraevaluar la conformidad, y 9 Procedimientos para la Evaluación de la Conformidad. Petitorio:solicitamos de la manera más comedida incluir como parte de los pliegos que los oferentes incluyanen sus propuestas los certificados de conformidad de las Tapas de Pozos y Rejillas ofertadas acordescon lo establecido en el Reglamento Técnico Ecuatoriano RTE-INEN-062 vigente, como sellos de calidad INEN tanto para los bienes como para los materiales eleborados.

answer: Respuesta 39.-Estimado Oferente favor remitirse a los pliegos.  Además sujétese a la ACLARACION 1 Y ACLARACION 2.

description: Con relación al rotulado y marcado de Tapas de Pozos y Rejillas, el Reglamento Técnico EcuatorianoRTE-INEN-062 vigente en su numeral 5. Requisitos de Marcado, Rotulado y Embalaje, establece estosrequerimientos. Petitorio: solicitamos de la manera más comedida incluir como parte de los pliegosel requerimiento obligatorio de marcado y rotulado de Tapas de Pozos y Rejillas ofertados segúnRTE-INEN-062 vigente.

answer: Respuesta 40.-Estimado Oferente favor remitirse a los pliegos.  Además sujétese a la ACLARACION 1 Y ACLARACION 2.

description: Pregunta: Como puede garantizar la entidad Contratante la calidad y durabilidad de un producto como una ?TAPA DE HA PARA POZO D=700MM? TAPA Y BROCAL TIPO A. Petitorio: solicitamos de la manera más comedida que se evidencie y certifique que el producto que consta en los pliegos y presupuesto referencial cumple con las Normas y Reglamentos Técnicos Ecuatorianos que están vigentes y además que disponen de la conformidad del Laboratorio Acreditado del INEN.

answer: Respuesta 41.-Estimado Oferente favor remitirse a los pliegos.  Además sujétese a la ACLARACION 1 Y ACLARACION 2.

description: Sabía Usted, que la Garantía Técnica de los productos usados en procesos de obras de infraestructura de Compras Públicas debe tener una vigencia de 10 años contra defectos de fabricación, Petitorio, solicitamos de la manera más comedida que la Entidad Contratante incluya en los pliegos que el proveedor y/o fabricante de Tapas y Rejillas de alcantarillado a ser usadas en el proceso LICO-EPEMAPAA-02-20, entregue una garantía Técnica de 10 años contra defectos de diseño y fabricación de los productos que serán ofertados.

answer: Respuesta 42.-Estimado Oferente favor remitirse a los pliegos.  Además sujétese a la ACLARACION 1 Y ACLARACION 2.

description: Independientemente del material para las tapas de pozos y rejillas seleccionado por la entidad: Hierro Dúctil, Acero, Hormigón, entre otros, las mismas deben cumplir los ensayos de cargas establecidos en las normas técnicas ecuatorianas: flecha residual y carga total, a ser efectuados en el Laboratorio Acreditado del INEN según las normas técnicas ecuatorianas NTE-INEN-2496 y NTE-INEN-EN-124:2019. Los ingenieros y funcionarios técnicos de la entidad responsable del proceso de compras públicas deberán tomar en consideración que los materiales de mayor resistencia permiten diseñar y fabricar Tapas de Pozos y Rejillas más livianas y su ventaja ergonómica para la instalación y mantenimiento seguridad y salud ocupacional de su personal. Petitorio: solicitamos de la manera más comedida considerar la inclusión en las especificaciones de Tapas de Pozos y Rejillas del presente proceso el material Hierro Nodular Grado 80-55-06, según la norma técnica ecuatoriana NTE-INEN-2499 vigente.

answer: ACLARACION 1: Se corrige el ANEXO EXPERIENCIA MINIMA PERSONAL TECNICO RESIDENTES DE OBRA, en la experiencia del residentes de obra 1 numeral 5 y residentes de obra 2 numeral 5, en el porcentaje de validación de la experiencia, por lo que se adjunta el ANEXO EXPERIENCIA MINIMA PERSONAL TECNICO CORREGIDO.

description: ACLARACION

answer: ACLARACION 2: En el  pliego, en el numeral 4.1.7. Metodología y cronograma de ejecución del proyecto en el ítem No. 1, en la Descripción se elimina la última frase MINIMO: 2 FRENTES DE TRABAJO.  Por lo que se solicita se remitan al ANEXO METODOLOGÍA Y CRONOGRAMA DE EJECUCIÓN DEL PROYECTO.

description: ACLARACION

name: TAPROCOM PROYECTOS Y CONSTRUCCIONES S.A.

description: ALCANTARILLADO SANITARIO Y PLUVIAL AV. BENJAMIN FRANKLIN

ROSAS CASTRO CARLOS ROMAN

streetAddress: LLUSHAPA ORIANGA OE1-29 CHAUPICRUZ (LA CONCEPCION)

Tufiño Peralta Javier Alejandro

streetAddress: BOLIVAR MANUELA CAÑIZARES 08 28 AMBATO, CABECERA CANTONAL Y CAPITAL PROVINCIAL

GRANDA LOAIZA DIEGO ADRIANO

streetAddress: CANTON ZAPOTILLO CARLOS ARIZAGA TORAL S/N YANUNCAY

ALOMIA CASTRO DIEGO SEBASTIAN

streetAddress: GUAYAS S/N LA TRONCAL, CABECERA CANTONAL

VILLAVICENCIO GONZALEZ JORGE EUGENIO

streetAddress: GIL RAMIREZ DAVALOS LUIS DAVILA SN TENA, CABECERA CANTONAL Y CAPITAL PROVINCIAL

COSTA & MOSER S. A.

streetAddress: FRANCISCO DE ORELLANA TARQUI 133 TENA, CABECERA CANTONAL Y CAPITAL PROVINCIAL

CONDO RAMIREZ SEGUNDO RODRIGO

streetAddress: JOSE JUSSIEU ISMAEL SOLIS. CONJUNTO RESIDENCIAL GERANIOS CASA 2 CONOCOTO

JARAMILLO CARDENAS GORKY AUGUSTO

streetAddress: CALLE ESPAÑA Y JUAN GENARO JARAMILLO A UNA CUADRA DEL GAD DE RUMIÑAHU s/n SANGOLQUI

Toscano Galarza Hector Ramiro

streetAddress: AV JULIO JARAMILLO ROGELIO RAMOS SN PICAIGUA

streetAddress: SANTA ROSA FERNANDO MAGALLANES OE6-68 SANTA PRISCA

legalName: TAPROCOM PROYECTOS Y CONSTRUCCIONES S.A.

ASPHALTVIAS CIA.LTDA

streetAddress: N32D PEDRO PONCE CARRASCO AV. DIEGO DE ALMAGRO E8-06 EL BATAN

MORENO CAICEDO JULIO IVAN

streetAddress: Calle Junin Av. Los Andes 110 HUACHI LORETO

Toscano Cadena Hector Rene

streetAddress: PASAJE JUAN TANCA MARENGO AVENIDA JULIO ENRIQUE PAREDES S/N ATOCHA ¿ FICOA

REYES GAMBOA ROY ALAN

streetAddress: 23 DE OCTUBRE JORGE SALGUERO S/N SANTIAGO, CABECERA CANTONAL

PAZMIÑO PATIÑO MIGUEL ANGEL

streetAddress: MONTAGO BYE SAN FRANCISCO CASA N1 IZAMBA

LANDA RUMIPAMBA WILMER ANTONIO

streetAddress: 6 DE DICIEMBRE LOS LAURELES, A UNA CUADRA DEL ESTADIO S/N CUYUJA

LASCANO PIZARRO MIGUEL ANGEL

streetAddress: Av. Bolivariana Isabela s/n AMBATO, CABECERA CANTONAL Y CAPITAL PROVINCIAL

rationale: ALCANTARILLADO SANITARIO Y PLUVIAL AV. BENJAMIN FRANKLIN