title: 000002/W/NRT/2023/2024/RHA

description: Construction works of the High Level Isolation Unit

description: Works

description: works

description: 150 mm thick wall

scheme: UNSPSC

description: 150 mm thick wall

description: Rendered walls externally

description: Rendered walls externally

description: 300mm thick wall

description: 300mm thick wall

description: Sides; Shear walls

description: Sides; Shear walls

description: Columns

description: Columns

description: Shear wall

description: Shear wall

description: 200 mm thick Slab

description: 200 mm thick Slab

description: 350KVA Oil indoor Transformers 15kV CU, Three way 15kV Modular-Extensible Compact MV switchgear consisting of one incomer circuit breaker SF6 (630A) & Two Outgoing, SF6 insulated Vacuum circuit breakers with self- powered relay having Transformer protection, over current and earth fault protection complete with instrumentation, protection and controls, and all attachments and accessories. As to Netral/ Schneider Electric Manufacture or approved equivalent

description: Door size 750 x 2200mm high;

description: Door size 750 x 2200mm high;

description: Standard SCHINDLER Model 3300AP MRL -Ex China Passenger lift or any other similar approved brand with capacity of 1000 kg 13 Passengers; with 3 stops; speed 1.0m/s; 1 door: 900mm . Complete with AVR unit, emergency drop off system, full load control and earthquake control.

description: Supply installation, Testing & Commissioning of RMS 480w Power amplifier, battery voltage 24Vdc (max. 10% deviation) Frequency response 60Hz to 15kHz (+1/-3dB) Inputs XLR & Phone Jack, SIN >85dB, as per detailed technical specification etc as required.

description: Preliminaries and General conditions

description: Preliminaries and General conditions

description: Supply installation, Testing & Commissioning of Intelligent Addressable Photoelectric Smoke Detector, UL listed 9th edition, Dual LED’s for 360 visibility, Advanced detection and communication protocol, Regular 100mm base, Address setting by 8 digit DIP switch, Operating Voltage17 ~ 28V DC, Reset Voltage, less than 3V, Start-Up Current, 500 μA Alarm Current, 5 am, Remote Output, 2mA maximum open collector, Operating Temperature, 10 C to 37.8 C, Humidity-0 - 95% RH, non-condensing, Smoke Sensitivity : (2.12 ± 0.61) % / ft, High : 1.1% ft, Middle : 1.4% ft, Low : 2.3% ft, Air Velocity : 0 - 4000 fpm,IP Rating : IP – 42 .

id: Supply and installation of Negative Pressure Ventillation System (NPVS)

description: Sensor Plantroom, 8 Port Hub

description: Sensor Plantroom, 8 Port Hub

description: Providing and fixing 6mm thick bevelled edge plate glass mirror of approved quality with 6mm thick marine ply backing fixed to wooden cleats with CP brass screws and washers.(Including s/s studs for fixing the glass). (Make: Jaquar, Cat no.-C8617 80X60 OR Equivalent)

description: 50mm dia conduit (1.6mm thick)

description: 50mm dia conduit (1.6mm thick)

title: 000002/W/NRT/2023/2024/RHA

status: complete

title: External Infrastructure

title: Amended Tender Document

title: Tender Document

title: Architecture

title: ME DrawingsP

title: Technical Specification

title: Negative Pressure Ventilation System

title: External Infrastructure

title: Adjusted TD with Clarification

title: Adjusted TD

title: Adjusted TD

title: Non  objection Response from RPPA

title: Architecture

title: External Infrastructure

title: MEP Drawings

title: Negative Pressure Ventilation System

title: Structure Data

title: Technical Specifications

procurementMethod: limited

mainProcurementCategory: works

Rwanda Housing Authority (RHA)

region: Kigali; Gasabo; Kacyiru

locality: Kigali; Gasabo; Kacyiru

postalCode: 2469 Kigali

countryName: Rwanda

streetAddress: Kigali; Gasabo; Kacyiru

scheme: TIN

legalName: Rwanda Housing Authority (RHA)

RWANDA BIO-MEDICAL CENTER(RBC)

roles: buyer procuringEntity

region: Gasabo District

locality: Gasabo District

postalCode: 7162 Kigali

streetAddress: Gasabo District

legalName: RWANDA BIO-MEDICAL CENTER(RBC)

HYGEBAT  LTD

region: KIGALI

locality: KIGALI

streetAddress: KIGALI

legalName: HYGEBAT  LTD

REAL CONTRACTORS  LTD

region: KG 5 AVENUE, KACYIRU SOUTH

locality: KG 5 AVENUE, KACYIRU SOUTH

postalCode: 4374 KIGALI-RWANDA

streetAddress: KG 5 AVENUE, KACYIRU SOUTH

legalName: REAL CONTRACTORS  LTD

STRONG CONSTRUCTIONS  LTD

legalName: STRONG CONSTRUCTIONS  LTD

HORIZON CONSTRUCTION  LTD

region: 4th Floor M&M Plaza, GISHUSHU, KG 8 Street

locality: 4th Floor M&M Plaza, GISHUSHU, KG 8 Street

streetAddress: 4th Floor M&M Plaza, GISHUSHU, KG 8 Street

legalName: HORIZON CONSTRUCTION  LTD

E.G.C Ltd

region: KG175ST - REMERA - DISTRICT OF GASABO - KIGALI CITY

locality: KG175ST - REMERA - DISTRICT OF GASABO - KIGALI CITY

streetAddress: KG175ST - REMERA - DISTRICT OF GASABO - KIGALI CITY

legalName: E.G.C Ltd

description: CENTRAL TREASURY

rationale: Construction works of the High Level Isolation Unit

name: Excavate for Pad foundation, commencing from reduced level; not exceeding 1.5m (0.3m) metres deep.

name: Approved (Minimum CBR 7) imported soil filling to make up levels : compacted in 150mm thick layers, compact each layer to 95% MDD to engineers approval.

name: Keeping excavations free of water, other than subterranean water; by pumping, bailing or other means necessary.

name: Anti termite TERMIDOR 25EC or equal and approved chemical anti termite treatment applying to: bottom and sides for trenches,etc,including forming and poisoning shallow furrows against foundation walls etc,filling in furrows and ramming with a 20 years

name: 1000 gauge polythene damp proof membrane; 300 mm wide laps.

name: Supply and Apply two coat of master seal 621 around Pad foundation sides, as per manufacture's instructions.

name: Supply , fix metallic plate balustrades together with all finishing works and paintings as per Architect's details and instructions

name: Supply, assemble and fix high quality 10mm thick flat temered/ thoughened glass well fixed to stainless steel 60mm diameter balusters spaced at 1160mm C/C with flaged bottom end screweded/bolted to concrete frames and top fixed to 45mm diameter stainless steel hand railing with all necessary welding, crips and decoration all to the architect's details and approvals.

name: Supply ,and fix metallic plate balustrades together with all finishing works and paintings as per Architect's details and instructions

name: Supply, assemble and fix high quality 10mm thick flat temered/ thoughened glass well fixed to stainless steel 60mm diameter balusters spaced at 1160mm C/C with flaged bottom end screweded/bolted to concrete frames and top fixed to 45mm diameter stainless steel hand railing with all necessary welding, crips and decoration all to the architect's details and approvals'.

name: Excavate for foundations starting from stripped level ( inclluding triming for the differing levels not excceednig 3.0m (2) metres deep

name: Extra over for excavating in Class 1 rock

name: 300mm Approved (Minimum CBR 7) imported soil filling to make up levels: compacted in 150mm thick layers, compact each layer to 95% MDD to engineers approval

name: Load and cart away excavated materials to approved Local Authority damp site to a distance approximately  10km away

name: Allow a provisional sum of Anti termite TERMIDOR 25EC or equal and approved chemical anti termite treatment applying to: bottom and sides for trenches,etc,including forming and poisoning shallow furrows against foundation walls etc,filling in furrows and ramming with a 20 years

name: IT5 roofing sheet gauge 26 ; roof coverings; pitch not exceeding 20 degree from horizontal; with ridge caps including framed structural steelwork to B.S. 5950 and 4360: 80x40x1.5mm RHS main tusses, 40x40x1.5mm intermediate SHS, 30x30x1.5mm SHS purlins; with and including welded connections : one coat red oxide primer before erection

name: 200x200mm lintel, reinforced with and including four 12mm diameter mild steel rods and 6mm stirrups at 200mm centres

name: Ditto, Perforated solid Burnt brick façade

name: Prepare and apply 5-6mm thick Rhino Wallmaster or T3 wallmaster to rendered walls.

name: 9 mm Thick dropped suspended gypsum ceiling fixed on and including brandering in Metal galvanised framing at 600x600mm centres both ways and including all necessary hangers, screws, skimmer coat and painting works

name: 10mm work to walls or concrete; trowelled to receive ceramic wall tiles.

name: Supply and fix 300 x 600 x 10mm thick coloured ceramic glazed wall tiles to walls on prepared backgrounds (m.s)

name: 50mm thick to receive floor finishes ....

name: 20mm thick, to receive finish; skirting 100mm high

name: Grade and compact subgrade, 98% BS heavy as described, to receive roads pavement layers.

name: Stabilised imported Murram base in layers of not more than 150mm compacted to 98% BS Heavy of compaction at optimum moisture content, 150 mm thick.

name: 150mm thick base course approved selected Latterite granular mixture as per BS EN 14227-1 compacted to 98% BS heavy

name: supplly and lay 30mm thick quarry dust bedding as described, laid and compacted by surface vibration.

name: Medium duty paving blocks size 210x105x60mm (minimum strength 30N/mm2) layed on all walkways and roads as described all as per engineer's details and instructions

name: Supply and lay  1000x150x 300mm Kerb type T2, half battered on one corner whrere necessary, supplied by Approved manufacturer; laid on and including concrete (1:3:6) base size 450 x 100 mm and 225 x 100 mm haunched up behind,  all as per Engineer's details and instructions

name: Loosen top 400mm of soil before adding topsoil

name: 100mm thick vegetable soil over general planting areas

name: Incorporate into top soil, farm yard manure 25mm thick and agricultural lime to adjust PH as necessary.

name: Provision for super phosphate over all planting areas

name: Supply and plant approved passpalum, Trees and Shrubs including watering until established with all necessary treatments as instructructed by landcaping architect

name: Water to be supplied by client during maintenance period of 3 months

name: Brick masonry fencing on natural stone bases with concrete coping including finishing; all as per architect's details

name: Allow a provisional sum for automatic barrier gate on both exit/entry gate

name: 50mm blinding under the Retaining wall bases

name: Balustrade 1100mm high comprising 40 x 40 x 1.5mm SHS handrail welded intermediate rails; or equivalent design to be provided by contractor, the whole with one coat red oxide primer to detail.

name: Supply, installation, testing, commissioning of the following Light Circuit with 1.5 sq.mm PVC insulated copper conductor 1100 volts grade stranded flexible wires in concealed/surface mounted PVC Conduit including cost of cutting & filling chases/ saddle, clamps, inspection/solid bends, switches etc. The cost of circuit wiring with 3 x 1.5 Sqmm PVC insulated copper conductor 1100 Volts grade wires shall be included in the cost of circuit wiring. (Cost of fish wire also to be included in the item) FOR LIGHTING CIRCUIT and according to design plans.

name: Suplying, installation, testing, commissioning of the 16 Amp Power Circuit with PVC insulated copper conductor 1100 volts grade stranded flexible wires in concealed/surface mounted PVC Conduit/ ceiling or floor mounted raceway including cost of cutting and filling chases as required with providing & fixing of 3 pin 16 Amps shuttered modular switch socket, with internal wiring, earthing of 3rd pin. The wiring shall be done with 3 x 2.5 Sqmm copper flexible wire and looping shall be done with 2.5 Sqmm. FOR NORMAL POWER SOCKETS CIRCUIT and according to design plans.

name: Supplyying, installation, testing, commissioning of the TV plug & socket outlet recess/ surface mounted type, complete with all inter connection, with PVC insulated copper conductor wires in concealed/surface mounted PVC Conduit including cost of cutting and filling chases as required with fixing of coaxial cable (40Meters Average per point). FOR TV and according to designed plans.

name: 4x6 Sq mm, PVC insulated copper wires in conduits

name: 1x4 Sq.mm PVC, insulated Y/G copper wires in conduits

name: main wiring with all the required material for the Tree phases power meter connection complete with all necessary accessories including. To be supplied by EUCL.

name: Steel, Supports Supplying and fixing  fabricated steel items like cable supports, MS clamps, hangers, frames etc. made of MS angles/flats, duly painted with primer and two or more coats of enamel paint including drilling holes cutting, bending tapping, threading etc. complete in all respects as per site requirement.

name: 12 ays TPN DB  - Patient LevelComprising of following:Incoming:Two (1) No.150 A FP MCB RCDOutgoing:                                                                                Two (2) Nos. 10A SP MCB RCDTwo (2) Nos. 16A SP MCB RCB                                                                                Eleventh (11) Nos. 50A 4P MCB     Neutral link:Separate for each outgoingEarthing Terminals:Earthing terminals suitable for 8 Nos. outgoing.

name: Type A - 600x600mm, 64Watts/4000k IP40 Ceiling Surface LED Panel light fitting

name: Type F - Ceiling, pendant decorative LED Light with 25Watts /3000k.

name: Type, G -Ceiling surface mounted LED Downlight with 12Watts /900Lm /3000k

name: Type I - Wall mounted, Up and Down LED Light fitting with 2x8Watts / 3000k Aluminium powder coated.

name: Type J - 234mm, Dia'. ceiling surface mounted LED Downligh with 9Watts / 4000k / 122Lm / IP40

name: Type K - 600mm Wall mounted LED Tube Light fitting with 8Watts, / 4000k / 125lM / IP40

name: Type M - Free stand LED Light fitting with 2x40Watts

name: Type N-280x280mm Wall mounted LED Light with 10Watts / 950Lm / 4000k.

name: Type O - Free stand LED Light fitting with 69 Watts

name: Type Q - 1250mmm Ceiling surface LED Tube light fitting with 62Watts / 8500Lm / 4000k / IP65

name: Type S - 140mm Dia. Ceiling pendant Down- light LED Fittting with 34Watts / 3000k / 4000Lm

name: Type V - 600x600mm ceilling mounted LED Panel fitting with 4000k / IP65.

name: Type X - 260x260mm, ceiling surface mounted LED Panel with 10Watts / 4000k / 600Lm.

name: Type Y - Wall suraface mounted LED Light fitting with ,13Watts / 4000k / 32Lm/W

name: Type Z - Wall, Surface 'mounted LED Light with 18Watts / 3000k / 100Lm/W.

name: Type B - Wall Ceiling suspended LED Exit SignLight with 9Watts

name: 16A Universal Single Power Outlet Socket with appropriate MK Box

name: 16A Universal Double Powers Outlet Socket with appropriate MK Box

name: 16A Three phase socket (Surface Industrial socket).

name: 32A Three phase' socket (Surface Industrial socket)

name: The Contractor, shall supply and install 40 LED FLAT TV with wall brackets as shown in the drawings or as instructed by the consultant

name: Supply installation, Tesing & Commissioning of Intelligent Addressable Photoelectric Smoke Detector, UL listed 9th edition, Dual LED’s for 360 visibility, Advanced detection and communication protocol, Regular 100mm base, Address setting by 8 digit DIP switch, Operating Voltage17 ~ 28V DC, Reset Voltage, less than 3V, Start-Up Current, 500 μA Alarm Current, 5 am, Remote Output, 2mA maximum open collector, Operating Temperature, 10 C to 37.8 C, Humidity-0 - 95% RH, non-condensing, Smoke Sensitivity : (2.12 ± 0.61) % / ft, High : 1.1% ft, Middle : 1.4% ft, Low : 2.3% ft, Air Velocity : 0 - 4000 fpm,IP Rating : IP – 42 .

name: Supply installation, Testing & Comissioning of Intelligent Addresable Photoelectric Heat Detector, UL listed 9th edition, Dual LED’s for 360 visibility, Advanced detection and communication protocol, Regular 100mm base, Address setting by 8 digit DIP switch, Operating Voltage17 ~ 28V DC, Reset Voltage, less than 3V, Start-Up Current, 500 μA Alarm Current, 5 am, Remote Output, 2mA maximum open collector, Operating Temperature, 10 C to 37.8 C, Humidity-0 - 95% RH, non-condensing, Smoke Sensitivity : (2.12 ± 0.61) % / ft, High : 1.1% ft, Middle : 1.4% ft, Low : 2.3% ft, Air Velocity : 0 - 4000 fpm,IP Rating : IP – 42 .

name: Supply installation, Testing & Comissioning of Intelligent Addressable Relay Module  UL-Listed (9th Edition), for AHU/Lift Shaft/Lift Lobby & stairs Pressurization Fan, Module Addressing by 8 way DIP switches, Low Standby Current, Available with suitable back boxes, Operating Voltage : 24 VDC Nominal Current Draw : 2 mA Max.(Latched), Standby Current : 0.5 mA, Contact Rating : 2A @ 30VDC(Resistive), Teperature Range : 0 DegreeC to 49 Degree C, Humidity, / 32- 120F, 93 ± 2% RH (non-condensing) at 32 ±2° C / 90 ±3° F, Dimensions : (95 W X 75 H X 24D)mmMake Ravel

name: Supplys installation, Testing & Commissioning of Addressable Manual Call Point, UL listed 9th Edition,Type A Indoor Use, Resettable by an element kit, Suitable for flush or surface mounting, Module Addressing by 8 way DIP Switches, Low Standby Current, Temperature : 0 - 49 OC, Relative Humidity : 0 - 95% non-condensing, Connection : 2.5mm2 Max, Weight : 125g, IP Rating : IP 53, Dimension : 92mm X 92mm X 48 mm.

name: Supplying installation, Testing & Commmissioning of Sounder cum Strobe, UL Listed 9th Edition, Operates on 24VDC, 100db, Ceiling / Flush Wall Mount,Input Voltage : 24V DC (15-30V), Current : 100 mA @24V, Relative Humidity : 93 ± 2 @ 32 C, Operating Temperature : -10 to 50 C, Sound Level : 112 db +/- 5dB @ 30cm, Tone Type : Sweep Siren, Size : 126(W)*126(H)*55(D),mm.

name: 2x1.0mm sq Fire resistantes Cable for detectors

name: 10mm work to, walls or concrete trowelled to receive porcelain wall tiles.

name: 2x1.0mm sq Fire resistante Cable Sounders,

name: Supply, Installation, Testing & Commissioning of D1 25/20fps Fixed Dome Camera, Vari-focal 3.3-12 mm, 4 Mega Pixel Resolution, builtin 12 IR lED, Viewing range up to 15 meter, H.264,True Day Night, support local storage with Sd card, PoE, ONVIF interface DC12V/AC24V,HIDC-P-1100EIRV with comprehensive I/O port,. Mic in, audio out, Video out, support various protocol RTSP, UPnP, 3GPP, HTTPS, Samba, all accessories like tamper proof screws, clamps, wiring etc. complete as requireds......

name: Supply, Installation, Testing & Commissioning of 4MP 25/20fps IP Fixed True Day/Nights inbuilt IR Box Camera with Vari-focal 3-12mm, H.264, PoE, DC12V/AC24V, HICC-P-1100EIRV ONVIF with all accessories like Outdoor weatherproof Housing, brackets, tamper proof screws, clamps, wiring etc. complete, as required.

name: CAT 6 F/UTP ,Copper Cable Slate Jacket, 4 Pair Count. Average length 30meter/point

name: Supply installation, Testing and Commissionig of NVR Server with Dual Core CPU for recording, playback and network performance, built in web server to support upto  64 Nos Cameras and software as per the system requirement. The Sytem shall have a storage capacity of 24/7 & 3 months backup, H.264 compression, video out put with HDMI/ VGA  Port, with multiscreen display ,network function HTTP, TCP/IP, UPNP, RTSP, UDP, SMTP, NTP, DHCP, DNS, IP Filter, HD-NVR-132, PPPOE,DDNS, FTP, Alarm Server, ethernet port RG-45(10/100/1000), 2 USB  PORT, RS-485/RS-232 complet as required.

name: Supply, Installation, Testing  and Commissioning of 32 Flat Color Monitors.

name: Supply , installation, testing  and  commissioning of SMPS Power supply .

name: MANAGED ETHERNET SWITCHES Supply, installation, testing and comissionning of Layer 2 managed switch with 24 ports (RJ-45),POE as to support all cameras and having 20% spare ports  complete with supply. The switch shall have 1 GB port to communicate with other switches including Passive components  inbuilt 2 SFP ports including SFP modules, POE compliant ports,  rack mountable, SMPS power supply & other accessories  complete as per specifications and as required.

name: Supply  and  installation, Testing & Commissioning of RMS 480w Power amplifier, battery voltage 24Vdc (max. 10% deviation) Frequency response 60Hz to 15kHz (+1/-3dB) Inputs XLR & Phone Jack, SIN >85dB, as per detailed technical specification etc as required.

name: Supply, installatiion, Testing & Commissioning of speaker 20W Ceiling Speaker complete with all accessories.

name: Supply and installation of selected 6 to 8mm thick ceramic wall tiles.

name: Supply, installation, Testing & Commissioning; of Controller Voltage VAS 230VAC, ±15%, 50/60 Hz, power consumption 600 VA, Voltage 24 VDC, +15% / -15% Output power RMS 240 W/360W, Frequency response 60 Hz to 18 kHz (+1/-3 dB at -10 dB ref rated output), Connector XLR, 6.3 mm jack, Sensitivity 1 mV (mic), 1 V (line),, 255 messages, format WAV-file, 16-bit PCM, mono, Memory capacity 16 MB Flash ROM, as per detailed technical specification as required.

name: Supply installation, Testing & Commissoing of Keypads station Voltage  18 to 24 VDC or VAC external power supply, Current consumption <30 mA (plus <15 mA per keypad) Input sound level (max) 110 dB, SPL Frequency response 100 Hz to 16 kHz, Speech filter -3dB at 315 Hz, high-pass, 6 dB/oct, Output impedance 200 ohm, expandable upto 8 units, as per detailed technical specification as required.

name: Supply installation, Testing and, Commissoing of Rated power 12w, Volume Control Attenuation step 5x3db+off, Frequency response 50Hz to 20kHz (-1 dB) as per detailed technical specification as required.

name: Supply installation, Testing & Commissoing of MS Equipement Rack (21U) to place the Amplifiers, Player, and motioned all the above devises, having regulated power supply strip for all the devices, door lock and key, openable from front and rear, and required devises as per detailed technical specification as required.

name: Supply, installation, Testing & Commissioning, of Sound system cablling with suitable shielded copper conductor cables for speakers as per detailed technical specification etc as per required.

name: Supply and fix IT5 roofing sheet gauge 26 ; roof coverings; pitch not exceeding 45 degree Approx. from horizontal; with ridge caps including framed structural steelwork to B.S. 5950 and 4360: 80x40x1.5mm RHS main trusses, 40x40x1.5mm intermediate SHS, 30x30x1.5mm SHS purlins; Including all necessarywelds,site welds, cleats, bolts, rivets, plates and sundry fixings, priming with red oxideprimer, painting of exposed steelwork with 3 coata glossoil paint, delivered to site and fix in position all as per structural Engineer details:

name: Supply, Installation, Testing & Commissioning Free- Stand Cistern with dual flush Actuator,,flush-stop function, noise less float valve and fast filling action with all component parts of high quality complete including fixing frame and set as required , (Cistern Make: Jaquar, Cat no.-WHT-31801011XD OR Equivalent), (Flushing Plate Make: Jaquar, Cat no.-CIS-CHR-31204019)

name: Supply, Innstallation, Testing & Commissioning vitreous Pedestial/Cabinet wash basin, specially fabricated brackets painted white and connection pipe to wall with C.P. wall flange and rubber adopter for waste connection complete, including cutting and making good the walls wherever required. (Make: Jaquar, Cat no.-FLS-WHT-0401 OR Equivalent)

name: Supply,, Installation, Testing & Commissioning C.P. brass Bottle trap 32 mm dia. with 75 mm clear water seal fitted with built-in Air Admittance valve of adequate capacity. (Make: Jaquar, Cat no.-ALD-769L250X190 OR Equivalent)

name: Supply, Installation,Testing & Commissioning 15 mm push, Single level, Basin mixer with Popup waste for Wash Basin complete including cutting, making and all accessories as required. (Make: Jaquar, Cat no.-KUP-CHR-35051BPM)

name: Supply, Installation, Testing & Commissioning C.P. brass towel, ring Square fixed to wooden / PVC cleats with C.P. brass screws including cutting and making good the walls wherever required. (Make: Jaquar, Cat no.-ACN-1121N OR Equivalent)

name: Supply, Installation, Testing & Commissioning, C.P. Brass toilet paper holder, including cutting and making good the walls wherever required. (Make: Jaquar, Cat no.-AHS-1553 OR Equivalent)

name: Supply, Installation, Testing & Commissioning,, 600 MM long 15mm dia Braided hose Connection Pipe with Two Nos. 15mm Nuts & Rubber Washer including making connections complet in all respects etc. as required. (Make: Jaquar, Cat no.-ALD-803AB OR Equivalent)

name: Supply, Installation, Testing & Commissioning C.P.brass angular stop cock regulating, valve with wall flange of standard design and of approved make conforming to IS:8931. (Make: Jaquar, Cat no.-COP-CHR-057PM OR Equivalent)

name: Providing and, fixing 6mm thick bevelled edge plate glass mirror of approved quality with 6mm thick marine ply backing fixed to wooden cleats with CP brass screws and washers.(Including s/s studs for fixing the glass). (Make: Jaquar, Cat no.-C8617 80X60 OR Equivalent)

name: Supply, Installation, Testing.  and commissioning C.P. Brass Towel holder, including, cutting and making good the walls wherever required. (Make: Jaquar, Cat no.-AHS-1553 OR Equivalent)

name: Supply, Installation, Testing & Commissioning Consealed Shower Mixer, including cutting and making good the walls wherever required. (Make: Jaquar, Cat no.-AHS-15 OR Equivalent).,

name: Supply, Installation, Testing & Commissioning Kitchen Sink, including cutting and making good the walls wherever required. (Make: Jaquar, Cat no.-AHS-1553 OR Equivalent),

name: Supply, Installation, Testing, & Commissioning Kitchen Sink Side singlr level Mono Sink mixer, including cutting and making good the walls wherever required. (Make: Jaquar, Cat no.-COP-CHR-179BPM; OR equivalent)

name: Supply and install 110 mm, dia. Four Way trap with Stainless steel FLOOR DRAIN cover.

name: Double Compartment Fire, cabinet  manufactured in mild steel,epoxy powder, 70 micron min painted red, complete with wall neceaasry brackets

name: Fire extinguishers (Dry chemical) 5kg all welded, 16swg steel body and handle fire extinguisher with textile reinforced noerane hose and high impact nozzle and strike knob. Multipurpose extinguisher rated for fire class A, B and C as manufactured by Angus Model AP 9K or approved equivalent.

name: Fire, extinguisher (CO2)9kg all welded 16swg steel body and handle fire extinguisher with textile reinforced noerane hose and high impact nozzle and strike knob. Multipurpose extinguisher rated for fire class A, B and C as manufactured by Angus Model AP 9K or approved equivalent.

name: Hose reel, 30m long, 20mm dia swinging access hose reel, including hexagonal union and gate valve for maintenance isolation of hose reel, as Angus Model 3 or approved equivalent

name: Canvas hose reel ;, of 2.5” x 30m, Diffuser nozzle 2.5” Inlet, 450 Ipm@7bar (or equivalent)

name: Hydrant, Cabinet Model no NHC 900 Cabinet dimensions W=90cm H=100cm D=25cm, Height of legs 60cm from floor level, Fire hoses Nos, of 2.5” x 30m, Diffuser nozzle 2.5” Inlet, 450 Ipm@7bar (or equivalent)

name: Hydrant Cabinet, Model no NHC 900 Cabinet dimensions W=90cm H=100cm D=25cm, Height of legs 60cm from floor level, Fire hoses Nos, of 2.5” x 30m, Diffuser nozzle 2.5” Inlet, 450 Ipm@7bar (or equivalent)

name: Two-way Breeching Inlet valve hand wheel  Spheroidal Graphite Cast Iron to BSEN 1563 : 1997 in a dry riser cabinet

name: 20mm thick to receive finich; treads with 300mm wide

name: 20mm thick to receive, finish; risers  with 170mm high

name: Supply, installation, testing and commissioning of the Complete Oxygen Plant with all necessary accessories.

name: Supply, installation, testing and commissioning of the ,Chroiline Solution Plant complete with all necessary accessories

name: Supply, installation, testing and commissioning, of the, Osmosis Solution Plant complete with all necessary accessories

name: Provision, amount for General testing and commissioning

name: Supplying, installation, testing, comissioning of the following Light Circuit with 1.5 sq.mm PVC insulated copper conductor 1100 volts grade stranded flexible wires in concealed/surface mounted PVC Conduit including cost of cutting & filling chases/ saddle, clamps, inspection/solid bends, switches etc. The cost of circuit wiring with 3 x 1.5 Sqmm PVC insulated copper conductor 1100 Volts grade wires shall be included in the cost of circuit wiring. (Cost of fish wire also to be included in the item) FOR LIGHTING CIRCUIT and according to design plans.

name: 20mm, thick to receive finish; skirting with 100mm high

name: Supplying, installation, testing, commissioning of the 16 Amp Power Circuit with PVC insulated copper conductor 1100 volts grade stranded flexible wires in concealed/surface mounted PVC Conduit/ ceiling or floor mounted raceway including cost of cutting and filling chases as requird with providing & fixing of 3 pin 16 Amps shuttered modular switch socket, with internal wiring, earthing of 3rd pin. The wiring shall be done with 3 x 2.5 Sqmm copper flexible wire and looping shall be done with 2.5 Sqmm. FOR NORMAL POWER SOCKETS CIRCUIT an according to design plans.

name: Supplyiing, installation, testing, commissioning of the TV plugs & socket outlet recess/ surface mounted type, complete with all inter connection, with PVC insulated copper conductor wires in concealed/surface mounted PVC Conduit including cost of cutting and filling chases as required with fixing of coaxial cable (40Meters Average per point). FOR TV and acccording to design plans.

name: 4x6 Sq.mm PVC insulated, copper wires in conduits

name: 1x4 Sq.mm; PVC insulated Y/G copper wires in conduits

name: Main wiring, with all the required material for the Tree phases power meter complete with all necessary accessories including. To be supplied by EUCL.

name: 20mm thick to receive finishh; Edges: outer strings

name: Steel Supports ;Supplying and fixing  fabricated steel items like cable supports, MS clamps, hangers, frames etc. made of MS angles/flats, duly painted with primer and two or more coats of enamel paint including drilling holes cutting, bending tapping, threading etc. complete in all respects as per site requirement.

name: 12 Ways TPNDB - Patient  of followig:Incoming:Two (1) No.100 A FP MCB RCDOutgoin:                                                                                Ten (10) Nos. 10A SP MCB RCDTwelve (12) Nos. 16A SP MCB RCB                                                                                Neutral link:Separate for each outgoingEarthing Terminals:Earthing terminals suitable for 8 Nos. outgoing.

name: 4 Ways TPN DB - Patient of following:Incoming:Two (1) No.125 A FP MCB RCDOutgoing:                                                                                Two (2) Nos. 10A SP MCB RCDThree (2) Nos. 16A SP MCB RCB                                                                                Two (3) Nos. 25A SP MCB RCDNeutral link:Separate for each outgoingEarthing Terminals:Earthing terminals suitable for 8 No. outgoing.

name: Type, A - 600x600mm 64Watts/4000k IP40 Ceiling Surface LED Panel light fitting

name: Type F -Ceiling, pendant decorative LED Light with 25Watts /3000k.

name: Type G - Ceiling surface , mounted LED Downlight with 12Watts /900Lm /3000k

name: Type I - Wall, mounted Up and Down LED Light fitting with 2x8Watts / 3000k Aluminium powder coated.

name: Type 'J - 234mm, Dia. Ceiling surface mounted LED Downligh with 9Watts / 4000k / 122Lm / IP40

name: Type K - 600mm, Wall mounted LED Tube Light fitting with 8Watts / 4000k / 125lM / IP40

name: Types M - Free stand LED Light fitting with 2x40Watts.

name: Type N - 280x280mm, Wall mounted LED Light with 10Watts / 950Lm / 4000k.

name: Type O - Free stand LED, Light fitting with 69Watts.

name: Typ Q - 1250mm; ceiling, surface LED Tube light fitting with 62Watts / 8500Lm / 4000k / IP65

name: Type S - 140mm.. Dia. Ceiling pendant Down light LED Fittting with 34Watts / 3000k / 4000Lm

name: Type V - 600x600mm Ceiling mounted LED Panel fitting with 4000k / IP65.....

name: Type X - 260 x260mm, Ceiling surface mounted LED Panel with 10Watts / 4000k / 600Lm.

name: Type Y - Wall suraface mounted LED, Light fitting with 13Watts / 4000k / 32Lm/W

name: Type Z - Walls, Surface mounted LED Light with 18Watts / 3000k / 100Lm/W.

name: Type B - Wall/Ceiling suspended, LED Exit SignLight with 9Watts

name: 16A Universal, Signle Power Outlet Socket with appropriate MK Box

name: 16A Universal Double, Power Outlet Socket with appropriate MK Box

name: 16A Three- phase socket (Surface Industrial socket)

name: 32A Three phases socket (Surface Industrial socket)

name: The Contractor, shall supply & install 40 LED FLAT TV with wall brackets as shown in the drawings or as instructed by the consultant

name: Supply installation, Testing & Commissioning of Intelligent Addressable Photoelectric Smoke Detector, UL listed 9th edition, Dual LED’s for 360 visiblity, Advanced detection and communication protocol, Regular 100mm base, Address setting by 8 digit DIP switch, Operating Voltage17 ~ 28V DC, Reset Voltage, less than 3V, Start-Up Current, 500 μA Alarm Current, 5 am, Remote Output, 2mA maximum open collector, Operating Temperature, 10 C to 37.8 C, Humidity-0 - 95% RH, non-condensing, Smoke Sensitivity : (2.12 ± 0.61) % / ft, High : 1.1% ft, Middle : 1.4% ft, Low : 2.3% ft, Air Velocity : 0 - 4000 fpm,IP Rating : IP – 42 .

name: Supply installation, Testing & Commissioning of Intelligent Addressable Photoelectric Heat Detector, UL listed 9th edition, Dual LED’s for 360 visibility, Advanced detection and communication protocol, Regular 100mm base, Address seting by 8 digit DIP switch, Operating Voltage17 ~ 28V DC, Reset Voltage, less than 3V, Start-Up Current, 500 μA Alarm Current, 5 am, Remote Output, 2mA maximum open collector, Operating Temperature, 10 C to 37.8 C, Humidity-0 - 95% RH, non-condensing, Smoke Sensitivity : (2.12 ± 0.61) % / ft, High : 1.1% ft, Middle : 1.4% ft, Low : 2.3% ft, Air Velocity : 0 - 4000 fpm,IP Rating : IP – 42 .

name: Supply installation, esting & Commissioning of Intelligent Addressable Relay Module  UL-Listed (9th Edition), for AHU/Lift Shaft/Lift Lobby & stairs Pressurization Fan, Module Addressing by 8 way DIP switches, Low Standby Current, Available with suitable back boxes, Operating Voltage : 24 VDC Nominal Current Draw : 2 mA Max.(Latched), Standby Current : 0.5 mA, Contact Rating : 2A @ 30VDC(Resistive), Temperature Range : 0 DegreeC to 49 Degree C, Humidity, / 32- 120F, 93 ± 2% RH (non-condensing) at 32 ±2° C / 90 ±3° F, Dimensions : (95 W X 75 H X 24D) mm. Make Ravel

name: Supply installation, Testing, & Commissioning of Addressable Manual Call Point, UL listed 9th Edition,Type A Indoor Use, Resettable by an element kit, Suitable for flush or surface mounting, Module Addressing by 8 way DIP Switches, Low Standby Current, Temperature : 0 - 49 OC, Relative Humidity : 0 - 95% non-condensing, Connection : 2.5mm2 Max, Weight : 125g, IP Rating : IP 53, Dimension: 92mm X 92mm X 48 mm.

name: Supply installation, Testing & Commissionning of Sounder cum Strobe, UL Listed 9th Edition, Operates on 24VDC, 100db, Ceiling / Flush Wall Mount,Input Voltage : 24V DC (15-30V), Current : 100 mA @24V, Relative Humidity : 93 ± 2 @ 32 C, Operating Temperature : -10 to 50 C, Sound Level : 112 db +/- 5dB @ 30cm, Tone Type : Sweep Siren, Size : 126(W)*126(H)*55(D)mm.

name: 2x1.0mm sq Fire, resistante Cable for detectors

name: Supply and fix rectangular stainless metalic expanded metal sheets with approved size and manufacturer CZZK or simillar

name: 2x1.0mm sq Fire resistante; Cable Sounders

name: Supply, Installation, Testing & Commissioning of D1 25/20fps, Fixed Dome Camera, Vari-focal 3.3-12 mm, 4 Mega Pixel Resolution, builtin 12 IR lED, Viewing range up to 15 meter, H.264,True Day Night, support local storage with Sd card, PoE, ONVIF interface DC12V/AC24V,HIDC-P-1100EIRV with comprehensive I/O port,. Mic in, audio out, Video out, support various protocol RTSP, UPnP, 3GPP, HTTPS, Samba, all accessories like tamper proof screws, clamps, wiring etc. complete as required.

name: Supply, Installation, Testing & Commissioning of 4MP... 25/20fps IP Fixed True Day/Night inbuilt IR Box Camera with Vari-focal 3-12mm, H.264, PoE, DC12V/AC24V, HICC-P-1100EIRV ONVIF with all accessories like Outdoor weatherproof Housing, brackets, tamper proof screws, clamps, wiring etc. complete as required.

name: CAT 6 F/UTP Copper, Cable Slate Jacket, 4 Pair Count. Average length 30meter/point

name: Supply installaton, Testing and Commissioning of NVR Server with Dual Core CPU for recording, playback and network performance, built in web server to support upto  64 Nos Cameras and software as per the system requirement. The System shall have a storage capacity of 24/7 & 3 months backup, H.264 compression, video out put with HDMI/ VGA  Port, with multiscreen display ,network function HTTP, TCP/IP, UPNP, RTSP, UDP, SMTP, NTP, DHCP, DNS, IP Filter, HD-NVR-132, PPPOE,DDNS, FTP, Alarm Server, ethernet port RG-45(10/100/1000), 2 USB  PORT, RS-485/RS-232 coplete as required.

name: Supply, Installation, Testing & Commissioning, of 32 Flat Color Monitors.

name: Supply , installation, testing & commissioning of SMPS Power supply ..

name: MANAGED ETHERNET SWITCHES Supply, installation, testing and commissioning of Layer 2 managed switch with 24 ports (RJ-45),,POE as to support all cameras and having 20% spare ports  complete with supply. The switch shall have 1 GB port to communicate with other switches including Passive components  inbuilt 2 SFP ports including SFP modules, POE compliant ports,  rack mountable, SMPS power supply & other accessories  complete as per specifications and as required.

name: Supply.. installation, Testing & Commissioning of RMS 480w Power amplifier, battery voltage 24Vdc (max. 10% deviation) Frequency response 60Hz to 15kHz (+1/-3dB) Inputs XLR & Phone Jack, SIN >85dB, as per detailed technical specification etc as required.

name: Supply; installation, Testing & Commissoing of speaker 20W Ceiling Speaker complete with all accessories.

name: Supply installation and Testing and commissioning of Controller Voltage VAS 230VAC, ±15%, 50/60 Hz, power consumption 600 VA, Voltage 24 VDC, +15% / -15% Output power RMS 240 W/360W, Frequency response 60 Hz to 18 kHz (+1/-3 dB at -10 dB ref rated output), Connector XLR, 6.3 mm jack, Sensitivity 1 mV (mic), 1 V (line), 255 messages, format WAV-file, 16-bit PCM, mono, Memory capacity 16 MB Flash ROM, as per detailed technical specification as required.

name: Supply installation,. Testing & Commissoing of Keypad station Voltage  18 to 24 VDC or VAC external power supply, Current consumption <30 mA (plus <15 mA per keypad) Input sound level (max) 110 dB, SPL Frequency response 100 Hz to 16 kHz, Speech filter -3dB at 315 Hz, high-pass, 6 dB/oct, Output impedance 200 ohm, expandable upto 8 units, as per detailed technical specifications as required.

name: Supply installation, Testing & Commissoing of Rated power ,12W Volume Control Attenuation step 5x3db+off, Frequency response 50Hz to 20kHz (-1 dB) as per detailed technical specification as required.

name: Supply installation, Testing & Commissoing of MS Equipment Rack (21U) to place the Amplifiers, Player, and motioned all the above devises, having regulated power supply strip for all the devices, door lock and key, openable from front and rear, and required devises as per detailed technical specification as required.

name: Supply  and installation, Testing & Commissoing of Sound system cabling with suitable shielded copper conductor cables for speakers as per detailed technical specification etc as per required.

name: Supply, Installation, Testing & Commissioning Free Stand Cistern with dual flush Actuator, flush-stop functions, noise less float valve and fast filling action with all component parts of high quality complete including fixing frame and set as required. (Cistern Make: Jaquar, Cat no.-WHT-31801011XD OR Equivalent), (Flushing Plate Make: Jaquar, Cat no.-CIS-CHR-31204019)

name: Supply, Installation, Testing & Commissioning vitreous Pedestial/Cabinet wash basin, specially fabricated brackets painted white and connections pipes to wall with C.P. wall flange and rubber adopter for waste connection complete, including cutting and making good the walls wherever required. (Make: Jaquar, Cat no.-FLS-WHT-0401 OR Equivalent)

name: Supply, Installation, Testing & Commissioning C.P. brass, Bottle trap 32 mm dia. with 75 mm clear water seal fitted with built-in Air Admittance valve of adequate capacity. (Make: Jaquar, Cat no.-ALD-769L250X190 OR Equivalent)

name: Supply, Installation,Testing & Commissioning 15 mm push Single level Basin, mixer with Popup waste for Wash Basin complete including cutting, making and all accessories as required. (Make: Jaquar, Cat no.-KUP-CHR-35051BPM),,

name: Supply, Installation, Testing & Commissioning C.P. brass towel ring Square fixed, to wooden / PVC cleats with C.P. brass screws including cutting and making good the walls wherever required. (Make: Jaquar, Cat no.-ACN-1121N O,R Equivalent)

name: Supply, Installation, Testing & Commissioning C.P. Brass toilet paper holder, including cutting and making good the walls wherever, required. (Make: Jaquar, Cat no.-AHS-1553 or, Equivalent)

name: Supply, installation, Testing & Commissioning 600 MM long 15mm dia Braided hose Connection Pipe with Two Nos. 15mm Nuts & Rubber Washer including making connections complet in all respects etc. as required. (Make: Jaquar, Cat no.-ALD-803AB OR Equivalents)!

name: Supply, Installation, Testing & Commissioning C.P.brass angular stop cock regulating valve with wall flange of standard design and of approved make conforming to IS:8931. (Make: Jaquar, Cat no,-COP-CHR-057PM OR Equivalent)

name: Providing ,and fixing 6mm thick bevelled edge plate glass mirror of approved quality with 6mm thick marine ply backing fixed to wooden cleats with CP brass screws and washers.(Including s/s studs for fixing the glass). (Make: Jaquar, Cat no.-C8617 80X60 OR Equivalent)

name: Supply, Installation, Testing & Commissioning C.P. Brass Towel holder, including cutting and making good the walls wherever required. (Make: Jaquar, Cat no.-AHS-1553 OR Equivalent,).

name: Suply, Installation, Testing & Commissioning Consealed Shower Mixer, including cutting and making good the walls wherever required. (Make: Jaquar, Cat no.-AHS-15 OR Equivalent)

name: Supply, Instalation, Testing & Commissioning Kitchen Sink, including cutting and making good the walls wherever required. (Make: Jaquar, Cat no.-AHS-1553 OR Equiv,alent)

name: Supply, Installation, Testing & Commissioning Kitchen Sink . Side singlr level Mono Sink mixer, including cutting and making good the walls wherever required. (Make: Jaquar, Cat no.-COP-CHR-179BPM OR Equivalent)

name: Supply, and install 110 mm dia. Four Way trap with Stainless steel FLOOR DRAIN cover.

name: Double Compartments Fire cabinet manufactured in mild steel,epoxy powder, 70 micron min painted red, complete with wall neceaasry brackets

name: Fire extinguishers, (Dry chemical) 5kg all welded 16swg steel body and handle fire extinguisher with textile reinforced noerane hose and high impact nozzle and strike knob. Multipurpose extinguisher rated for fire class A, B and C as manufactured by Angus Model AP 9K or approved equivalent.

name: Fire extinguisher (CO2) with 9kg all welded 16swg steel body and handle fire extinguisher with textile reinforced noerane hose and high impact nozzle and strike knob. Multipurpose extinguisher rated for fire class A, B and C as manufactured by Angus Model AP 9K or approved equivalent.

name: Hose reel, 30m, long, 20mm dia swinging access hose reel, including hexagonal union and gate valve for maintenance isolation of hose reel, as Angus Model 3 or approved equivalent

name: Canvas hoses reel  , of 2.5” x 30m, Diffuser nozzle 2.5” Inlet, 450 Ipm@7bar (or equivalent)

name: Hydrants Cabinet Model no NHC 900 Cabinet dimensions W=90cm H=100cm D=25cm, Height of legs 60cm from floor level, Fire hoses Nos, of 2.5” x 30m, Diffuser nozzle 2.5” Inlet, 450 Ipm@7bar (or equivalent)

name: Hydrant, Cabinet, Model no NHC 900 Cabinet dimensions W=90cm H=100cm D=25cm, Height of legs 60cm from floor level, Fire hoses Nos, of 2.5” x 30m, Diffuser nozzle 2.5” Inlet, 450 Ipm@7bar (or equivalent)

name: Two ways Breeching Inlet valve, hand wheel  Spheroidal Graphite Cast Iron to BSEN 1563 : 1997 in a dry riser cabinet

name: Supply, installlation, testing and commissioning of the Complete Oxygen Plant with all necessary accessories

name: Supply, installation, testing and commissioning of the Chroiline Solution Plant complete with all necessary accessories.,;

name: Supply, installation, testing and commissioning of the Osmosis Solution Plant complete with all necessary accessories,

name: Provision ,amount for General testing and commissioning

name: Supplying, instalation, testing, commissioning of the following Light Circuit with 1.5 sq.mm PVC insulated copper conductor 1100 volts grade stranded flexible wires in concealed/surface mounted PVC Conduit including cost of cutting & filling chases/ saddle, clamps, inspection/solid bends, switches etc. The cost of circuit wiring with 3 x 1.5 Sqmm PVC insulated copper conductor 1100 Volts grade wires shall be included in the cost of circuit wiring. (Cost of fish wire also to be included in the item) FOR LIGHTING CIRCUIT and according to design plans.

name: Supplying, installation, testing, commisioning of the 16 Amp Power Circuit with PVC insulated copper conductor 1100 volts grade stranded flexible wires in concealed/surface mounted PVC Conduit/ ceiling or floor mounted raceway including cost of cutting and filling chases as required with providing & fixing of 3 pin 16 Amps shuttered modular switch soket, with internal wiring, earthing of 3rd pin. The wiring shall be done with 3 x 2.5 Sqmm copper flexible wire and looping shall be done with 2.5 Sqmm. FOR NORMAL POER SOCKETS CIRCUIT and according to design plans.

name: Supplyiing, innstallation, testing, commissioning of the TV plug, & socket outlet recess/ surface mounted type, complete with all inter connection, with PVC insulated copper conductor wires in concealed/surface mounted PVC Conduit including cost of cutting and filling chases as required with fixing of coaxial cable (40Meters Average per point). FOR TV and according to design plans.

name: (4x6) Sq.mm PVC insulated copper wires in conduits

name: 1x4 Sq.mm 'PVC insulated Y/G copper wires in conduits

name: Main' wiring with all the required material for the Tree phases power meter complete with all necessary accessories including. To be supplied by EUCL.

name: Steel Supports Supplying and fixing  fabricated steel, items like cable supports, MS clamps, hangers, frames etc. made of MS angles/flats, duly painted with primer and two or more coats of enamel paint including drilling holes cutting, bending tapping, threading etc. complete in all respects as per site requirement.

name: 12 Ways TPN DB  - Patient LevelComprising of folowing:Incoming:Two (1) No.100 A FP MCB RCDOutgoing:                                                                                Ten (10) Nos. 10A SP MCB RCDTwelve (12) Nos. 16A SP MCB RCB                                                                                Neutral link:Separate for each outgoingEarthing Terminals:Earthing terminals suitable for 8 Nos. outgoing.

name: Type A - 600x600mm, 64Watts/4000k IP40 Ceiling Surface LED Panel light fitting.

name: Type F '- Ceiling pendant decorative LED Light with 25Watts /3000k.

name: Type G - Cei'ling surface mounted LED Downlight with 12Watts /900Lm /3000k

name: Type I - Wall mounted' Up and Down LED Light fitting with 2x8Watts / 3000k Aluminium powder coated.

name: Type J - 234mm Dia. ceiling surface mounted LED Downlight, with 9Watts / 4000k / 122Lm / IP40

name: Supply ; and installation of Purpose made powder coated fixed aluminium frame fabricated from approved sections (minimum 1.5mm thick) infilled wit Double sliding mosquito net/mesh for windows with no Laminates as per architect's details

name: Type K - 600mm Wall mounted LED Tube Light fitting with 8Watts / 4000k / 125lM / IP40'

name: Type M - Free' stand LED Light fitting with 2x40Watts.

name: Typ'e N - 280x280mm Wall mounted LED Light with 10Watts / 950Lm / 4000k.

name: Type O- Free stand LED Light fitting with 69Watts............

name: Type Q - 1250mm Ceiling surface, LED Tube light fitting with 62Watts / 8500Lm / 4000k / IP65

name: Type S - 140mm Dia. C'eiling pendant Down light LED Fittting with 34Watts / 3000k / 4000Lm

name: Type V - 600x600'mm Ceiling mounted LED Panel fitting with 4000k / IP65.

name: Type X - 260x260mm Ceilin'g surface mounted LED Panel with 10Watts / 4000k / 600Lm.

name: 'Type Y - Wall surface mounted LED Light fitting with 13Watts / 4000k / 32Lm/W

name: Type Z - Wall Surface' mounted LED Light with 18Watts / 3000k / 100Lm/W.

name: 200 x 200mm gutter shaped as required, including fixing, welding and brackets as required

name: Type B - Wall'/Ceiling suspeded LED Exit SignLight with 9Watts

name: 16A Universal Sing'le Power Outlet Socket with appropriate MK Box

name: 16A' Universal Double Power Outlet Socket with appropriate MK Box

name: 16A Three phase s'ocket (Surface Industrial socket)

name: 32A Three phase sock'et (Surface Industrial socket)

name: The' Contractor shall supply & install 40 LED FLAT TV with wall brackets as shown in the drawings or as instructed by the consultant

name: Supply installation, Testing & Commissioning of Intelligent Addressable Photoelectric Smoke Detector, UL listed 9th edition, Dual LED’s for 360 visibility, Advanced detection and communication protocol, Regular 100mm base, Address setting by 8 digit DIP switch, Operating Voltage17 ~ 28V DC, Reset Voltage, less than 3V, Start-Up Current, 500 μA Alarm Current, 5 am, Remote Output, 2mA maximum open collector, Operating Tmperature, 10 C to 37.8 C, Humidity-0 - 95% RH, non-condensing, Smoke Sensitivity : (2.12 ± 0.61) % / ft, High : 1.1% ft, Middle : 1.4% ft, Low : 2.3% ft, Air Velocity : 0 - 4000 fpm,IP Rating : IP – 42 .

name: Supply installation, Testing & Commissioning of Intelligent Addressable Photoelectric Heat Detector, UL listed 9th edition, Dual LED’s for 360 visibility, Advanced detection and communication protocol, Regular 100mm base, Address setting by 8 digit DIP switch, Operating Voltage17 ~ 28V DC, Reset Voltage, less than 3V, Start-Up Current, 500 μA Alarm Current, 5 am, Remote Output, 2mA maximum open collector, Operating Temperature, 10 C to 37.8 C, Humidity-0 - 95% RH, non-condensing, Smoke Sensitivity : (2.12 ± 0.61) % / ft, High : 1.1% ft, Middle : 1.4% ft, Low : 2.3% ft, Air Velocity : 0 - 4000 fpmIP Rating : IP – 42 .

name: Supply installation, Testing  Commissioning of Intelligent Addressable Relay Module  UL-Listed (9th Edition), for AHU/Lift Shaft/Lift Lobby & stairs Pressurization Fan, Module Addressing by 8 way DIP switches, Low Standby Current, Available with suitable back boxes, Operating Voltage : 24 VDC Nominal Current Draw : 2 mA Max.(Latched), Standby Current : 0.5 mA, Contact Rating : 2A @ 30VDC(Resistive), Temperature Range : 0 DegreeC to 49 Degree C, Humidity, / 32- 120F, 93 ± 2% RH (non-condensing) at 32 ±2° C / 90 ±3° F, Dimensions : (95 W X 75 H X 24Dmm.  Make Ravel

name: Supply installation and testing & Commissioning of Addressable Manual Call Point, UL listed 9th Edition,Type A Indoor Use, Resettable by an element kit, Suitable for flush or surface mounting, Module Addressing by 8 way DIP Switches, Low Standby Current, Temperature : 0 - 49 OC, Relative Humidity : 0 - 95% non-condensing, Connection : 2.5mm2 Max, Weight : 125g, IP Rating : IP 53, Dimension : 92mm X 92mm X 48 mm.

name: Supply insstallation, Testing & Commissioning of Sounder cum Strobe, UL Listed 9th Edition, Operates on 24VDC, 100db, Ceiling / Flush Wall Mount,Input Voltage : 24V DC (15-30V), Current : 100 mA @24V, Relative Humidity : 93 ± 2 @ 32 C, Operating Temperature : -10 to 50 C, Sound Level : 112 db +/- 5dB @ 30cm, Tone Type : Sweep Siren, Size : 126(W)*126(H)*55(D)mm.

name: 2x1.0'mm sq Fire resistante Cable for detectors

name: '2x1.0mm sq Fire resistante Cable Sounders

name: Supply, Installation, Testing & Commissioning of D1 25/20fps Fixed Dome Cameras, Vari-focal 3.3-12 mm, 4 Mega Pixel Resolution, builtin 12 IR lED, Viewing range up to 15 meter, H.264,True Day Night, support local storage with Sd card, PoE, ONVIF interface DC12V/AC24V,HIDC-P-1100EIRV with comprehensive I/O port,. Mic in, audio out, Video out, support various protocol RTSP, UPnP, 3GPP, HTTPS, Samba, all accessories like tamper proof screws, clamps, wiring etc. complete as required.

name: Supply, Installation, Testing & Commissioning of 4MP 25/20fps IP Fixed True Day/Night inbuilt IR Box Camera with vari-focal 3-12mm,.. H.264, PoE, DC12V/AC24V, HICC-P-1100EIRV ONVIF with all accessories like Outdoor weatherproof Housing, brackets, tamper proof screws, clamps, wiring etc. complete as required.

name: CAT 6 F/UTP' Copper Cable Slate Jacket, 4 Pair Count. Average length 30meter/point

name: Supply installation, Testing and Commissioning of NVR Server with Dual Core CPU for recording, playback and network performance, built in web server t support upto  64 Nos Cameras and software as per the system requirement. The System shall have a storage capacity of 24/7 & 3 months backup, H.264 compression, video out put with HDMI/ VGA  Port, with multiscreen display ,network function HTTP, TCP/IP, UPNP, RTSP, UDP, SMTP, NTP, DHCP, DNS, IP Filter, HD-NVR-132, PPPOE,DDNS, FTP, Alarm Server, ethernet port RG-45(10/100/1000), 2 USB  PORT, RS-485/RS-232 complete as required.

name: Supply, Installation', Testing & Commissioning of 32 Flat Color Monitors.

name: 'Supply , installation, testing & commissioning of SMPS Power supply

name: MANAGED ETHERNET SWITCHES Supply, installation, testing and commissioning of Layer 2 managed switches with 24 ports (RJ-45),POE as to support all cameras and having 20% spare ports  complete with supply. The switch shall have 1 GB port to communicate with other switches including Passive components  inbuilt 2 SFP ports including SFP modules, POE compliant ports,  rack mountable, SMPS power supply & other accessories  complete as per specifications and as required.

name: Supply,' installation, Testing & Commissioning of RMS 480w Power amplifier, battery voltage 24Vdc (max. 10% deviation) Frequency response 60Hz to 15kHz (+1/-3dB) Inputs XLR & Phone Jack, SIN >85dB, as per detailed technical specification etc as required.

name: 'Supply, installation, Testing & Commissoing of speaker 20W Ceiling Speaker complete with all accessories.

name: Suply installation, Testing & Commissoing of Controller Voltage VAS 230VAC, ±15%, 50/60 Hz, power consumption 600 VA, Voltage 24 VDC, +15% / -15% Output power RMS 240 W/360W, Frequency response 60 Hz to 18 kHz (+1/-3 dB at -10 dB ref rated output), Connector XLR, 6.3 mm jack, Sensitivity 1 mV (mic), 1 V (line), 255 messages, format WAV-file, 16-bit PCM, mono, Memory capacity 16 MB Flash ROM, as per detailed technical specification as required.

name: Supply installation, Testing & Commissioning of Keypad, station Voltage  18 to 24 VDC or VAC external power supply, Current consumption <30 mA (plus <15 mA per keypad) Input sound level (max) 110 dB, SPL Frequency response 100 Hz to 16 kHz, Speech filter -3dB at 315 Hz, high-pass, 6 dB/oct, Output impedance 200 ohm, expandable upto 8 units, as per detailed technical specification as required.

name: Supply, installation, Testing & Commissoing of Rated power 12w, Volume Control Attenuation step 5x3db+off, Frequency response 50Hz to 20kHz (-1 dB) as per detailed technical specification' as required.

name: Supply installation, Testing & Commissoing of MS Equipment Rack (21U) to place the Amplifier, Player, and motioned all the above devises, having regulated power supply strip for all the devices, door lock and key, openable from front and rear, and required devises as per detailed technical specification as required.

name: Supply installation, 'Testing & Commissoing of Sound system cabling with suitable shielded copper conductor cables for speakers as per detailed technical specification etc as per required.

name: Supply, Installation, Testing & Commissioning Free Stand Cistern with dual flush Actuator, flush-stop function, noise less float valve and fast filling action with all component parts of high- quality complete including fixing frame and set as required. (Cistern Make: Jaquar, Cat no.-WHT-31801011XD OR Equivalent), (Flushing Plate Make: Jaquar, Cat no.-CIS-CHR-31204019)

name: Supply, Installation, Testing & Commissioning vitreous Pedestial/Cabinets wash basin, specially fabricated brackets painted white and connection pipe to wall with C.P. wall flange and rubber adopter for waste connection complete, including cutting and making good the walls wherever required. (Make: Jaquar, Cat no.-FLS-WHT-0401 OR Equivalent)

name: Supply, Installation', Testing & Commissioning C.P. brass Bottle trap 32 mm dia. with 75 mm clear water seal fitted with built-in Air Admittance valve of adequate capacity. (Make: Jaquar, Cat no.-ALD-769L250X190 OR Equivalent)

name: Supply, Inst'allation,Testing & Commissioning 15 mm push Single level Basin mixer with Popup waste for Wash Basin complete including cutting, making and all accessories as required. (Make: Jaquar, Cat no.-KUP-CHR-35051BPM)

name: Supply, Installation, Testing & Commissioning C.P. brass towel ring Square fixed to wooden / PVC cleats with C.P. brass screws including cutting and making good the walls wherever required. (Make: Jaquar, Cat no.-ACN-1121N OR Equivalent)'

name: S'upply, Installation, Testing & Commissioning C.P. Brass toilet paper holder, including cutting and making good the walls wherever required. (Make: Jaquar, Cat no.-AHS-1553 OR Equivalent)

name: Supply, Install'ation, Testing & Commissioning 600 MM long 15mm dia Braided hose Connection Pipe with Two Nos. 15mm Nuts & Rubber Washer including making connections complet in all respects etc. as required. (Make: Jaquar, Cat no.-ALD-803AB OR Equivalent)

name: Sup'ply, Installation, Testing & Commissioning C.P.brass angular stop cock regulating valve with wall flange of standard design and of approved make conforming to IS:8931. (Make: Jaquar, Cat no.-COP-CHR-057PM OR Equivalent)

name: Providing and fixing 6mm thick bevelled edge plate glass mirror of approved quality, with 6mm thick marine ply backing fixed to wooden cleats with CP brass screws and washers.(Including s/s studs for fixing the glass). (Make: Jaquar, Cat no.-C8617 80X60 OR Equivalent)

name: Supply, Installation, Tes'ting & Commissioning C.P. Brass Towel holder, including cutting and making good the walls wherever required. (Make: Jaquar, Cat no.-AHS-1553 OR Equivalent)

name: Supply, Installation, T'esting & Commissioning Consealed Shower Mixer, including cutting and making good the walls wherever required. (Make: Jaquar, Cat no.-AHS-15 OR Equivalent)

name: Supply, Installati'on, Testing & Commissioning Kitchen Sink, including cutting and making good the walls wherever required. (Make: Jaquar, Cat no.-AHS-1553 OR Equivalent)

name: Suppl'y, Installation, Testing & Commissioning Kitchen Sink Side singlr level Mono Sink mixer, including cutting and making good the walls wherever required. (Make: Jaquar, Cat no.-COP-CHR-179BPM OR Equivalent)

name: Supply and install 110' mm dia. Four Way trap with Stainless steel FLOOR DRAIN cover.

name: Double Compat'ment Fire cabinet  manufactured in mild steel,epoxy powder, 70 micron min painted red, complete with wall neceaasry brackets

name: Fire extinguishers (Dry chemmical) 5kg all welded 16swg steel body and handle fire extinguisher with textile reinforced noerane hose and high impact nozzle and strike knob. Multipurpose extinguisher rated for fire class A, B and C as manufactured by Angus Model AP 9K or approved equivalent.

name: 10mm work; to walls or concrete trowelled to receive porcelain wall tiles.

name: Fire extinguissher (CO2)9kg all welded 16swg steel body and handle fire extinguisher with textile reinforced noerane hose and high impact nozzle and strike knob. Multipurpose extinguisher rated for fire class A, B and C as manufactured by Angus Model AP 9K or approved equivalent.

name: Hose reel 30'm long, 20mm dia swinging access hose reel, including hexagonal union and gate valve for maintenance isolation of hose reel, as Angus Model 3 or approved equivalent

name: Canvas hose' reel  , of 2.5” x 30m, Diffuser nozzle 2.5” Inlet, 450 Ipm@7bar (or equivalent)

name: Hyd'rant Cabinet Model no NHC 900 Cabinet dimensions W=90cm H=100cm D=25cm, Height of legs 60cm from floor level, Fire hoses Nos, of 2.5” x 30m, Diffuser nozzle 2.5” Inlet, 450 Ipm@7bar (or equivalent)

name: Hydrant Ca'binet Model no NHC 900 Cabinet dimensions W=90cm H=100cm D=25cm, Height of legs 60cm from floor level, Fire hoses Nos, of 2.5” x 30m, Diffuser nozzle 2.5” Inlet, 450 Ipm@7bar (or equivalent)

name: Two way Bre'eching Inlet valve, hand wheel  Spheroidal Graphite Cast Iron to BSEN 1563 : 1997 in a dry riser cabinet

name: Supply and installation of selected 6mm thick ceramic wall tiles...

name: Supply, installation, te'sting and commissioning of the Complete Oxygen Plant with all necessary accessories

name: Supply, installation, testing and commissioning of the Chroiline Solution Plant complete with all necessary accessori'es

name: Supply, insttallation, testing and commissioning of the Osmosis Solution Plant complete with all necessary accessories

name: Supplying, instllation, testing, commissioning of the following Light Circuit with 1.5 sq.mm PVC insulated copper conductor 1100 volts grade stranded flexible wires in concealed/surface mounted PVC Conduit including cost of cutting & filling chases/ saddle, clamps, inspection/solid bends, switches etc. The cost of circuit wiring with 3 x 1.5 Sqmm PVC insulated copper conductor 1100 Volts grade wires shall be included in the cost of circuit wiring. (Cost of fish wire also to be included in the item) FOR LIGHTING CIRCUIT and according to design plans.

name: Suplying, instalation, testing, commissioning of the 16 Amp Power Circuit with PVC insulated copper conductor 1100 volts grade stranded flexible wires in concealed/surface mounted PVC Conduit/ ceiling or floor mounted raceway including cost of cutting and filling chases as required with providing & fixing of 3 pin 16 Amps shuttered modular switch socket, with internal wiring, earthing of 3rd pin. The wiring shall be done with 3 x 2.5 Sqmm coper flexible wire and looping shall be done with 2.5 Sqmm. FOR NORMAL POWER SOCKETS CIRCUIT and according to design plans.

name: Supplys, installation, testing, commissioning of the TV plug & socket outlet recess/ surface mounted type, completed with all inter connection, with PVC insulated copper conductor wires in concealed/surface mounted PVC Conduit including cost of cutting and filling chases as required with fixing of coaxial cable (40Meters Average per point). FOR TV and according to design plans.

name: 4x6 Sq.mm PVC insullated copper wires in conduits

name: 1x4 Sq.mm PVC insulated, Y/G copper wires in conduits

name: main wiring with' all the required material for the Tree phases power meter complete with all necessary accessories including. To be supplied by EUCL.

name: Steel Supports 'Supplying and fixing  fabricated steel items like cable supports, MS clamps, hangers, frames etc. made of MS angles/flats, duly painted with primer and two or more coats of enamel paint including drilling holes cutting, bending tapping, threading etc. complete in all respects as per site requirement.

name: 110 mm Diameter rainwater PVC down pipe complete with fittings,  brackets, primed and prepare and apply 3 coats gloss painted to approval.

name: 20mm thick to receive finishes ; andings

name: 12 Ways TPN DB  - Patient LevelComprising of following:Incoming:Two (1) No.150 A FP MCB RCDOutgoing:                                                                                Two (2) Nos. 10A SP MCB RCDTwo (2) Nos. 16A SP MCB RCB                                                                                Eleventh (11) Nos. 50A 4P MCB     Neutral link:Separate for each outgoingEarthing Terminals:Earthing terminals suitable for 8 No. outgoing.

name: 8 Ways TPN DB UPS - Patient LevelComprising of following:Incoming:Two (1) No.100 A FP MCB RCDOutgoing:                                                                                Twelve (12) Nos. 16A SP MCB RCB                                                                                Neutral link:Separate for each outgoingEarthing Terminals:Earthing terminals suitable for 8 Nos. outgoing.

name: Type A - 600x600mm; 64Watts/4000k IP40 Ceiling Surface LED Panel light fitting

name: Type F - Ceilin'g pendant decorative LED Light with 25Watts /3000k.

name: Type G - Ceiling s'urface mounted LED Downlight with 12Watts /900Lm /3000k

name: Type I - Wall mounted u'p and Down LED Light fitting with 2x8Watts / 3000k Aluminium powder coated.

name: Type J - 234mm Dia. Ceiling; surface mounted LED Downligh with 9Watts / 4000k / 122Lm / IP40

name: Type K - 600'mm Wall mounted LED Tube Light fitting with 8Watts / 4000k / 125lM / IP40

name: 20mm thick to receive finish; treads with 300mm wide

name: Type M - Free stand, LED Light fitting with 2x40Watts.

name: Types, N - 280x280mm Wall mounted LED Light with 10Watts / 950Lm / 4000k.

name: Type O - Free -stand LED Light fitting with 69Watts.

name: Type Q - 1250mm ceiling, surface, LED Tubes light fitting with 62Watts / 8500Lm / 4000k / IP65

name: Type S - 140mm 'Dia. Ceiling pendant Down light LED Fittting with 34Watts / 3000k / 4000Lm

name: Type V - 600x600mm Cei'ling mounted LED Panel fitting with 4000k / IP65.

name: Type X - 260x260mm C'eiling surface mounted LED Panel with 10Watts / 4000k / 600Lm.

name: Type Y - Wall surface mounted LED Light fitting with 13Watts / 4000k / 32Lm/W

name: Type Z - Wal'l Surface mounted LED Light with 18Watts / 3000k / 100Lm/W.

name: Type B - Wall/Ceiling suspeded LED Exit SignLight with 9Watts

name: 20mm thick to; receive finish; risers with  170mm high

name: 16A Universel Single Power Outlet Socket with appropriate MK Box

name: 16A ;Universal Double Power Outlet Socket with appropriate MK Box

name: 16A Three phaze socket (Surface Industrial socket)

name: 32A Tri- phase socket (Surface Industrial socket)

name: 20mm thik to receive finish; skirting  with 100mm high

name: The Contractor will supply & install 40 LED FLAT TV with wall brackets as shown in the drawings or as instructed by the consultant

name: Supply , Testing &  of Intelligent Addressable Photoelectric Smoke Detector, UL listed 9th edition, Dual LED’s for 360 visibility, Advanced detection and communication protocol, Regular 100mm base, Address setting by 8 digit DIP switch, Operating Voltage17 ~ 28V DC, Reset Voltage, less than 3V, Start-Up Current, 500 μA Alarm Current, 5 am, Remote Output, 2mA maximum open collector, Operating Temperature, 10 C to 37.8 C, Humidity-0 - 95% RH, non-condensing, Smoke Sensitivity : (2.12 ± 0.61) % / ft, High : 1.1% ft, Middle : 1.4% ft, Low : 2.3% ft, Air Velocity : 0 - 4000 fpm,IP Rating : IP – 42

name: Supply installation, Testing & Commissioning of Intelligent Addresable Photoelectric Heat Detector, UL listed 9th edition, Dual LED’s for 360 visibility, Advanced detection and communication protocol, Regular 100mm base, Address setting by 8 digit DIP switch, Operating Voltage17 ~ 28V DC, Reset Voltage, less than 3V, Start-Up Current, 500 μA Alarm Current, 5 am, Remote Output, 2mA maximum open collector, Operating Temperature, 10 C to 37.8 C, Humidity-0 - 95% RH, non-condensing, Smoke Sensitivity : (2.12 ± 0.61) % / ft, High : 1.1% ft, Middle : 1.4% ft, Low : 2.3% ft, Air Velocity : 0 - 4000 fpm,IP Rating : IP – 42 .

name: Supply installation, Testing & Commissioning of Intelligent ddressable Relay Module  UL-Listed (9th Edition), for AHU/Lift Shaft/Lift Lobby & stairs Pressurization Fan, Module Addressing by 8 way DIP switches, Low Standby Current, Available with suitable back boxes, Operating Voltage : 24 VDC Nominal Current Draw : 2 mA Max.(Latched), Standby Current : 0.5 mA, Contact Rating : 2A @ 30VDC(Resistive), Temperature Range : 0 DegreeC to 49 Degree C, Humidity, / 32- 120F, 93 ± 2% RH (non-condensing) at 32 ±2° C / 90 ±3° F, Dimensions : (95 W X 75 H X 24D) mm.  Make Ravel

name: Supply installations, Testing & Commissioning of Addressable Manual Call Point, UL listed 9th Edition,Type A Indoor Use, Resettable by an element kit, Suitable for flush or surface mounting, Module Addressing by 8 way DIP Switches, Low Standby Current, Temperature : 0 - 49 OC, Relative Humidity : 0 - 95% non-condensing, Connection : 2.5mm2 Max, Weight : 125g, IP Rating : IP 53, Dimension : 92mm X 92mm X 48 mm.

name: Supplying installation, Testing & Commissioning of Sounder cum Strobe, UL Listed 9th Edition, Operates on 24VDC, 100db, Ceiling / Flush Wall Mount,Input Voltage : 24V DC (15-30V), Current : 100 mA @24V, Relative Humidity : 93 ± 2 @ 32 C, Operating Temperature : -10 to 50 C, Sound Level : 112 db +/- 5dB @ 30cm, Tone Type : Sweep Siren, Size : 126(W)*126(H)*55(D)mm.

name: 2x1.0mm sq Fire resist'ante Cable for detectors

name: 2x1.0mm sq Fire resistante 'Cable Sounders

name: Supply, Installation, Testing & Commissioning of D1 25/20fps Fixed Dome Camera, Vari-focal 3.3-12 mm, 4 Mega Pixels Resolution, builtin 12 IR lED, Viewing range up to 15 meter, H.264,True Day Night, support local storage with Sd card, PoE, ONVIF interface DC12V/AC24V,HIDC-P-1100EIRV with comprehensive I/O port,. Mic in, audio out, Video out, support various protocol RTSP, UPnP, 3GPP, HTTPS, Samba, all accessories like tamper proof screws, clamps, wiring etc. complete as required.

name: Supply, Installation, Testing & Commissioning of 4MP 25/20fps IP Fixed True Day/Night inbuilt IR Box Camera with Vari-focal 3-12mm, H.264, PoE, DC12V/AC24V, HICC-P-1100EIRV ONVIF with all accessories like Outdoor weatherproof Housing, brackets, tamper proof screws, clamps, wiring etc. complete as required.

name: 20mm thick to receive finish; Edges: outer strings

name: CAT 6 F/UTP Copp'er Cable Slate Jacket, 4 Pair Count. Average length 30meter/point

name: Supply installation, Testing an Commissioning of NVR Server with Dual Core CPU for recording, playback and network performance, built in web server to support upto  64 Nos Cameras and software as per the system requirement. The System shall have a storage capacity of 24/7 & 3 months backup, H.264 compression, video out put with HDMI/ VGA  Port, with multiscreen display ,network function HTTP, TCP/IP, UPNP, RTSP, UDP, SMTP, NTP, DHCP, DNS, IP Filter, HD-NVR-132, PPPOE,DDNS, FTP, Alarm Server, ethernet port RG-45(10/100/1000), 2 USB  PORT, RS-485/RS-232 complete as required.

name: Supply, Installation, Te'sting & Commissioning of 32 Flat Color Monitors.

name: Sup'ply , installation, testing & commissioning of SMPS Power supply

name: MANAGED' ETHERNET SWITCHESSupply, installation, testing and commissioning of Layer 2 managed switch with 24 ports (RJ-45),POE as to support all cameras and having 20% spare ports  complete with supply. The switch shall have 1 GB port to communicate with other switches including Passive components  inbuilt 2 SFP ports including SFP modules, POE compliant ports,  rack mountable, SMPS power supply & other accessories  complete as per specifications and as required.

name: Supply installation, Testin'g & Commissioning of RMS 480w Power amplifier, battery voltage 24Vdc (max. 10% deviation) Frequency response 60Hz to 15kHz (+1/-3dB) Inputs XLR & Phone Jack, SIN >85dB, as per detailed technical specification etc as required.

name: Supply installation, Testing & Commissioning, of speaker 20W Ceiling Speaker complete with all accessories.

name: Supply installation, Testing & Commissoing of Controller Voltage VAS 230VAC, ±15%, 50/60 Hz, power consumption 600 VA, Voltage 24 VDC, +15% / -15% Output power RMS 240 W/360W, Frequency response 60 Hz to 18 kHz (+1/-3 dB at -10 dB Ref rated output), Connector XLR, 6.3 mm jack, Sensitivity 1 mV (mic), 1 V (line), 255 messages, format WAV-file, 16-bit PCM, mono, Memory capacity 16 MB Flash ROM, as per detailed technical specification as required.

name: Supply and installation, Testing & Commissoing of Keypad station Voltage  18 to 24 VDC or VAC external power supply, Current consumption <30 mA (plus <15 mA per keypad) Input sound level (max) 110 dB, SPL Frequency responses 100 Hz to 16 kHz, Speech filter -3dB at 315 Hz, high-pass, 6 dB/oct, Output impedance 200 ohm, expandable upto 8 units, as per detailed technical speccification as required.

name: Supply installati'on, Testing & Commissoing of Rated power 12w, Volume Control Attenuation step 5x3db+off, Frequency response 50Hz to 20kHz (-1 dB) as per detailed technical specification as required.

name: Supply installation, Testing & Commissioningg of MS Equipment Rack (21U) to place the Amplifiers, Player, and motioned all the above devises, having regulated power supply strip for all the devices, door lock and key, openable from front and rear, and required devises as per detailed technical specification as required.

name: Supply installation, Testing  and ' Commissoing of Sound system cabling with suitable shielded copper conductor cables for speakers as per detailed technical specification etc as per required.

name: Supply, Installation, Testing & Commissioning Frees Stand Cistern with dual flush Actuator, flush-stop function, noise less float valve and fast filling action with all component parts of high quality complete including fixing frame and set as required. (Cistern Make: Jaquar, Cat no.-WHT-31801011XD OR Equivalent), (Flushing Plate Make: Jaquar, Cat no.-CIS-CHR-31204019)

name: Supply, Installati'on, Testing & Commissioning vitreous Pedestial/Cabinet wash basin, specially fabricated brackets painted white and connection pipe to wall with C.P. wall flange and rubber adopter for waste connection complete, including cutting and making good the walls wherever required. (Make: Jaquar, Cat no.-FLS-WHT-0401 OR Equivalent)

name: Supply, Installation, Tessting & Commissioning C.P. brass Bottle trap 32 mm dia. with 75 mm clear water seal fitted with built-in Air Admittance valve of adequate capacity. (Make: Jaquar, Cat no.-ALD-769L250X190 OR Equivalent)

name: Supply, Installlation,Testing & Commissioning 15 mm push Single level Basin mixer with Popup waste for Wash Basin complete including cutting, making and all accessories as required. (Make: Jaquar, Cat no.-KUP-CHR-35051BPM)

name: Supply, Installattion, Testing & Commissioning C.P. brass towel ring Square fixed to wooden / PVC cleats with C.P. brass screws including cutting and making good the walls wherever required. (Make: Jaquar, Cat no.-ACN-1121N OR Equivalent)

name: Supply, Installation, Tessting & Commissioning C.P. Brass toilet paper holder, including cutting and making good the walls wherever required. (Make: Jaquar, Cat no.-AHS-1553 OR Equivalent)

name: Supply, Installation, Tesing & Commissioning 600 MM long 15mm dia Braided hose Connection Pipe with Two Nos. 15mm Nuts & Rubber Washer including making connections complet in all respects etc. as required. (Make: Jaquar, Cat no.-ALD-803AB OR Equivalent)

name: Su'pply, Installation, Testing & Commissioning C.P.brass angular stop cock regulating valve with wall flange of standard design and of approved make conforming to IS:8931. (Make: Jaquar, Cat no.-COP-CHR-057PM OR Equivalent)

name: Providing and fixing 6mm thick bevelled edge plate, glass mirror of approved quality with 6mm thick marine ply backing fixed to wooden cleats with CP brass screws and washers.(Including s/s studs for fixing the glass). (Make: Jaquar, Cat no.-C8617 80X60 OR Equivalent)

name: Supply, Installation, Testing & Commissioning C.P. Brass Towel, holder, including cutting and making good the walls, wherever required. (Make: Jaquar, Cat no.-AHS-1553 OR Equivalent)

name: Supply, Installation, Testing, & Commissioning Consealed Shower Mixer, including cutting and making good the walls wherever required. (Make: Jaquar, Cat no.-AHS-15 OR Equivalent)

name: Supply, Installation, Testing & Commissioning Kitchen Sink, including cutting and making good the walls wherever required. (Make: Jaquar, Cat no.-AHS-1553 OR Equivale'nt)

name: Supply, Installation, Testing & Commissioning Kitchen Sink Side singlr level Mono Sink mixer, including cutting and making good the walls wherever required. (Make: Jaquar, Cat no.-COP-CHR-179 BPM OR, Equivalent)

name: Supply and, install 110 mm dia. Four Way trap with Stainless steel FLOOR DRAIN cover.

name: Double, Compartment' Fire cabinet  manufactured in mild steel,epoxy powder, 70 micron min painted red, complete with wall neceaasry brackets

name: Fire extinguisher (CO2) 9kgs all welded 16swg steel body and handle fire extinguisher with textile reinforced noerane hose and high impact nozzle and strike knob. Multipurpose extinguisher rated for fire class A, B and C as manufactured by Angus Model AP 9K or approved equivalent.

name: Horse reel 30m long, 20mm dia swinging access hose reel, including hexagonal union and gate valve for maintenance isolation of hose reel, as Angus Model 3 or approved equivalent

name: Canvas horse reels  , of 2.5” x 30m, Diffuser nozzle 2.5” Inlet, 450 Ipm@7bar (or equivalent)

name: Hydrant_ Cabinet Model no NHC 900 Cabinet dimensions W=90cm H=100cm D=25cm, Height of legs 60cm from floor level, Fire hoses Nos, of 2.5” x 30m, Diffuser nozzle 2.5” Inlet, 450 Ipm@7bar (or equivalent)

name: Hydrant Cabinet Model No: NHC 900 Cabinet dimensions W=90cm H=100cm D=25cm, Height of legs 60cm from floor level, Fire hoses Nos, of 2.5” x 30m, Diffuser nozzle 2.5” Inlet, 450 Ipm@7bar (or equivalent)

name: Two-way Breeching Inlet valve, hand wheel  Spheroidal Graphite Cast Iron to BSEN 1563 : 1997 in a dry riser cabinet

name: Supply, instalation, testing and commissioning of the Complete Oxygen Plant with all necessary accessories

name: Extra over ditto for 110mm diameter outlet

name: Supply, installation, testing and commissioning of the Chroiline Solution Plant complete with all necessary accessories;

name: Supply, installation, testing and commissioning of the Osmosis Solution Plant complete with all necessary accesories

name: Provizion amount for Genaral testing and commissioning

name: Supplying, installation, testing, commissioning of the following Light Circuit with 1.5 sq.mm PVC insulated coper conductor 1100 volts grade stranded flexible wires in concealed/surface mounted PVC Conduit including cost of cutting & filling chases/ saddle, clamps, inspection/solid bends, switches etc. The cost of circuit wiring with 3 x 1.5 Sqmm PVC insulated copper conductor 1100 Volts grade wires shall be included in the cost of circuit wiring. (Cost of fih wire also to be included in the item) FOR LIGHTING CIRCUIT and according to design plans.

name: Spplying, installation, testing, commissioning of the 16 Amp Power Circuit with PVC insulated copper conductor 1100 volts grade stranded flexible wires in concealed/surface mounted PVC Conduit/ ceiling or floor mounted raceway including cost of cutting and filling chases as required with providing & fixing of 3 pin 16 Amps shuttered modular switch socket, with internal wiring, earthing of 3rd pin. The wiring shall be done with 3 x 2.5 Sqmm copper flexible wire and looping shall be done with 2.5 Sqmm. FOR NORMAL POWER SOCKETS CIRCUIT and according to design plans.

name: Supply, installation, tessting, commissioning of the TV plug & socket outlet recess/ surface mounted type, complete with all inter connection, with PVC insulated copper conductor wires in concealed/surface mounted PVC Conduit including cost of cutting and filling chases as required with fixing of coaxial cable (40Meters Average per point). FOR TV and according to Design plans....

name: 4x6 Sq.mm PVC insulated copper wires in conduits

name: 1x4 Sq.mm PVC insulated Y/G copper wires in conduits

name: main wiring with all the required material for the Tree phases power meter complete with all necessary accessories including. To be supplied by EUCL.

name: Steel, SupportsSupplying and fixing  fabricated steel items, like cable supports, MS clamps, hangers, frames etc. made of MS angles/flats, duly painted with primer and two or more coats of enamel paint including drilling holes cutting, bending tapping, threading etc. complete in all respects as per site requirement.

name: 12 Ways TPN DB  - Patient LevelComprising of following:Incoming:Two (1) No.150 A FP MCB RCDOutgoing:                                                                                Two (2) Nos. 10A SP MCB RCDTwo (2) Nos. 16A SP MCB RCB                                                                                Eleventh (11) Nos. 50A 4P MCB     Neutral link:Separate for each outgoingEarthing Terminals:Earthing terminals suitable for 8 Nos. outgoig.

name: 4 Ways TPN DB - Patient roomComprising of following:Incoming:Two (1) No.125 A FP MCB RCDOutgoing:                                                                                Two (2) Nos. 10A SP MCB RCDThree (2) Nos. 16A SP MCB RCB                                                                                Two (3) Nos. 25A SP MCB RCDNeutral link:Separate for each outgoingEarthing Terminals:Earthing terminals sutable for 8 Nos. outgoing.

name: Type A - 600x600mm 64Watts/4000k IP40 Ceiling Surface LED Panel light fitting

name: Type F - Ceiling pendant decorative LED Light with 25Watts /3000k.

name: Type G - Ceiling surface mounted LED Downlight with 12Watts /900Lm /3000k

name: Type I - Wall mounted Up and Down LED Light fitting with 2x8Watts / 3000k Aluminium powder coated.

name: Type J - 234mm Dia. Ceiling surface mounted LED Downligh with 9Watts / 4000k / 122Lm / IP40

name: Type K - 600mm Wall mounted LED Tube Light fitting with 8Watts / 4000k / 125lM / IP40

name: Type M - Free stand LED Light fitting with 2x40Watts.

name: Type N - 280 x 280mm Walls mounted LED Light with 10Watts / 950Lm / 4000k.

name: Type O - Free stand LED Light fitting with 69Watts.

name: Type Q - 1250mm Ceiling surface LED Tube light fitting with 62Watts / 8500Lm / 4000k / IP65

name: Type S - 140mm Dia. Ceiling pendant Down light LED Fittting with 34Watts / 3000k / 4000Lm

name: Type V - 600x600mm Ceiling mounted LED Panel fitting with 4000k / IP65.

name: Type X - 260x260mm Ceiling surface mounted LED Panel with 10Watts / 4000k / 600Lm.

name: Type Y - Wall suraface mounted LED Light fitting with 13Watts / 4000k / 32Lm/W

name: Type Z - Wall Surface mounted LED Light with 18Watts / 3000k / 100Lm/W.

name: 16A Universal Signle Power Outlet Socket with appropriate MK Box

name: 16A Universal Doublle, Power Outlet Socket with appropriate MK Box

name: 16A Three phase socket (Surface Industrial socket)

name: 32A Three phase socket (Surface Industrial socket)

name: The Contractor shall supply & install 40 LED FLAT TV with wall brackets as shown in the drawings or as instructed by the consultant

name: Supply installation, Testing & Commissioning of Intelligent Addressable Photoelectrc Smoke Detector, UL listed 9th edition, Dual LED’s for 360 visibility, Advanced detection and communication protocol, Regular 100mm base, Address setting by 8 digit DIP switch, Operating Voltage17 ~ 28V DC, Reset Voltage, less than 3V, Start-Up Current, 500 μA Alarm Current, 5 am, Remote Output, 2mA maximum open collector, Operating Temperature, 10 C to 37.8 C, Humidity-0 - 95% RH, non-condensing, Smoke Sensitivity : (2.12 ± 0.61) % / ft, High : 1.1% ft, Middle : 1.4% ft, Low : 2.3% ft, Air Velocity : 0 - 4000 fpm,IP Rating : IP – 42 .

name: Supply installation, Testing & Commissioning of Intelligent Addressable Photoelectric Heat Detector, UL listed 9th edition, Dual LED’s for 360 visibility, Advanced detection and communication protocol, Regular 100mm base, Address setting by 8 digit DIP switch, Operating Voltage17 ~ 28V DC, Reset Voltage, less than 3V, Start-Up Current, 500 μA Alarm Current, 5 am, Remote Output, 2mA maximum open collector, Operating Temperature, 10 C to 37.8 C, Humidity-0 - 95% RH, non-condensing, Smoke Sensitivity : (2.12 ± 0.61) % / ft, High : 1.1% ft, Midle : 1.4% ft, Low : 2.3% ft, Air Velocity : 0 - 4000 fpm,IP Rating : IP – 42 .

name: Supply installation, Testing & Commissioning of Intelligent Addressable Relay Module  UL-Listed (9th Edition), for AHU/Lift Shaft/Lift Lobby & stairs Pressurization Fan, Module Addressing by 8 way DIP switches, Low Standby Current, Available with suitable back boxes, Operating Voltage : 24 VDC Nominal Current Draw : 2 mA Max.(Latched), Standby Current : 0.5 mA, Contact Rating : 2A @ 30VDC(Resistive), Temperature Range : 0 DegreeC to 49 Degree C, Humidity, / 32- 120F, 93 ± 2% RH (non-condensing) at 32 ±2° C / 90 ±3° F, Dimensions : (95 W X 75 H X 24D) mm. Mak Ravel

name: Supply installation, Testing & Commissioning of Addressable Manual Call Point, UL listed 9th Edition,Type A Indoor Use, Resettable by an element kit, Suitable for flush or surface mounting, Module Addressing by 8 way DIP Switches, Low Standby Current, Temperature : 0 - 49 OC, Relative Humidity : 0 - 95% non-condensing, Connection : 2.5mm2 Max, Weight : 125g, IP Rating : IP 53, Dimension: 92mm X 92mm X 48 mm...

name: Supply installation, Testing & Commissioning of sounder, cum Strobe, UL Listed 9th Edition, Operates on 24VDC, 100db, Ceiling / Flush Wall Mount,Input Voltage : 24V DC (15-30V), Current : 100 mA @24V, Relative Humidity : 93 ± 2 @ 32 C, Operating Temperature : -10 to 50 C, Sound Level : 112 db +/- 5dB @ 30cm, Tone Type : Sweep Siren, Size : 126(W)*126(H)*55(D)mm.

name: 2x1.0mm sq Fire resistante Cable for detectors

name: 2x1.0mm sq Fire resistante Cable Sounders

name: Supply, Installation, Testing & Commissioning of D1 25/20fps Fixed Dome Camera, Vari-focal 3.3-12 mm, 4 Mega Pixel Rezolution, builtin 12 IR lED, Viewing range up to 15 meter, H.264,True Day Night, support local storage with Sd card, PoE, ONVIF interface DC12V/AC24V,HIDC-P-1100EIRV with comprehensive I/O port,. Mic in, audio out, Video out, support various protocol RTSP, UPnP, 3GPP, HTTPS, Samba, all accessories like tamper proof screws, clamps, wiring etc. complete as required.

name: Supply, Installation, Testing & Commissioning of 4MP 25/20fps IP Fixed True Day/Night inbuilt IR Box Camera with Vari-focal 3-12mm, H.264, PoE, DC12V/AC24V, HICC-P-1100EIRV ONVIF with all accessories like Outdoor weatherproof Housings, brackets, tamper proof screws, clamps, wiring etc,, complete as required.

name: CAT 6 F/UTP Copper Cable Slate Jacket, 4 Pair Count. Average length 30meter/point

name: Supply installation, Testing and Commissioning of NVR Server with Dual Core CPU for recording, playback and network performance, built in web server to support upto  64 Nos Cameras and software as per the system requirement. The System shall have a storage capacity of 24/7 & 3 months backup, H.264 compression, video out put with HDMI/ VGA  Port, with multiscreen display ,network function HTTP, TCP/IP, UPNP, RTSP, UDP, SMTP, NTP, DHCP, DNS, IP Filter, HD-NVR-132, PPPOE,DDNS, FTP, Alarm Server, ethernet port RG-45(10/100/1000), 2 USB  PORT, RS-485/RS-232 complete as required

name: Supply, Installation, Testing & Commissioning of 32 Flat Color Monitors.

name: Supply , installation, testing & commissioning of SMPS Power supply

name: MANAGED ETHERNET SWITCHES Supply, installation, testing and commissioning of Layer 2 managed switch, with 24 ports (RJ-45),POE as to support all cameras and having 20% spare ports  complete with supply. The switch shall have 1 GB port to communicate with other switches including Passive components  inbuilt 2 SFP ports including SFP modules, POE compliant ports,  rack mountable, SMPS power supply & other accessories  complete as per specifications and as required.

name: Supply installation, Testing & Commissioning of RMS 480w Power amplifier, battery voltage 24Vdc (max. 10% deviation) Frequency response 60Hz to 15kHz (+1/-3dB) Inputs XLR & Phone Jack, SIN >85dB, as per detailed technical specification etc as required.

name: Supply, and installation, Testing & Commissoing of speaker 20W Ceiling Speaker complete with all accessories.

name: Supply instal, Testing & Commissoing of Controller Voltage VAS 230VAC, ±15%, 50/60 Hz, power consumption 600 VA, Voltage 24 VDC, +15% / -15% Output power RMS 240 W/360W, Frequency response 60 Hz to 18 kHz (+1/-3 dB at -10 dB ref rated output), Connector XLR, 6.3 mm jack, Sensitivity 1 mV (mic), 1 V (line), 255 messages, format WAV-file, 16-bit PCM, mono, Memory capacity 16 MB Flash ROM, as per detailed technical specification as required.

name: Supply installation, Testing & Commissoing of Keypad station Voltage  18 to 24 VDC or VAC external power supply, Current consumption <30 mA (plus <15 mA per keypad) Input sound level (max) 110 dB, SPL Frequency response 100 Hz to 16 kHz, Speech filter -3dB at 315 Hz, high-pass, 6 dB/oct, Output impedance 200 ohm, expandable upto 8 units, as per detailed technical specification as required.!

name: Supply installation, Testing & Commissoing of Rated power 12w, Volume Control Attenuation step 5x3db+off, Frequency response 50Hz to 20kHz (-1 dB) as per detailed technical specification as required.

name: Supply installation, Testing & Commissoing of MS Equipment Rack (21U) to place the Amplifiers, Player, and motioned all the above devises, having regulated power supply strip for all the devices, door lock and key, openeble from front and rear, and required devises as per detailed technical specification as required.

name: Supply and installation of Purpose made powder coated Fixed aluminium frames fabricated from approved sections (minimum 1.5mm thick) infilled wit Double sliding mosquito net/mesh for windows with no Laminates as per details of arhitects!

name: Supply installation, Testing & Commissoing of Sound system cabling with suitable shielded copper conductor cables for speakers as per detailed technical specification etc as per required.

name: Supply, Installation, Testing & Commissioning Free Stand Cistern with dual flush Actuators, flush-stop function, noise less float valve and fast filling action with all component parts of high quality complete including fixing frame and set as required. (Cistern Make: Jaquar, Cat no.-WHT-31801011XD OR Equivalent), (Flushing Plate Make: Jaquar, Cat no.-CIS-CHR-31204019)

name: Supply, Installation, Testing & Commissioning vitreous Pedestial/Cabinet wash basins, specially fabricated brackets painted white and connection pipe to wall with C.P. wall flange and rubber adopter for waste connection complete, including cutting and making good the walls wherever required. (Make: Jaquar, Cat no.-FLS-WHT-0401 OR Equivalent)

name: Supply, Installation, Testing & Commissioning C.P. brass Bottle trap 32 mm dia. with 75 mm clear water seal fitted with built-in Air Admittance valve of adequate capacity. (Make: Jaquar, Cat no.-ALD-769L250X190 OR Equivalent)

name: Supply, Installation,Testing & Commissioning 15 mm push Single level Basin mixer with Popup waste for Wash Basin complete including cutting, making and all accessories as required. (Make: Jaquar, Cat no.-KUP-CHR-35051BPM)

name: Supply, Installation, Testing & Commissioning C.P. brass towel ring Square fixed to wooden / PVC cleats with C.P. brass screws including cutting and making good the walls wherever required. (Make: Jaquar, Cat no.-ACN-1121N OR Equivalent)

name: Supply, Installation, Testing & Commissioning C.P. Brass toilet paper holder, including cutting and making good the walls wherever required. (Make: Jaquar, Cat no.-AHS-1553 OR Equivalent)

name: Supply, installation, Testing & Commissioning 600 MM long 15mm dia Braided hose Connection Pipe with Two Nos. 15mm Nuts & Rubber Washer including making connections complet in all respects etc. as required. (Make: Jaquar, Cat no.-ALD-803AB or, Equivalent)

name: Supply, Installation, Testing & Commissioning C.P.brass angular stop cock regulating valve with wall flange of standard design and of approved make conforming to IS:8931. (Make: Jaquar, Cat no.-COP-CHR-057PM OR Equivalent)

name: Providing and fixing 6mm thick bevelled edge plate glass mirror of approved quality with 6mm thick, marine ply backing fixed to wooden cleats with CP brass screws and washers.(Including s/s studs for fixing the glass). (Make: Jaquar, Cat no.-C8617 80X60 OR Equivalent)

name: Supply, Installation, Testing & Commissioning C.P. Brass Towel holder, including cutting and making good the walls wherever required. (Make: Jaquar, Cat no.-AHS-1553 OR Equivalent)

name: Supply, Installation, Testing & Commissioning Consealed Shower Mixer, including cutting and making good the walls wherever required. (Make: Jaquar, Cat no.-AHS-15 OR Equivalent)

name: Supply, Installation, Testing & Commissioning Kitchen Sink, including cutting and making good the walls wherever required. (Make: Jaquar, Cat no.-AHS-1553 OR Equivalent)

name: Supply, Installation, Testing & Commissioning Kitchen Sink Side singlr level Mono Sink mixer, including cutting and making good the walls wherever required. (Make: Jaquar, Cat no.-COP-CHR-179BPM OR Equivalent)

name: Supply and install 110 mm dia. Four Way trap with Stainless steel FLOOR DRAIN cover.

name: Double Compatment Fire cabinet  manufactured in mild steel,epoxy powder, 70 micron min painted red, complete with wall neceaasry brackets

name: Fire extinguishers (Dry chemical) 5kg all welded 16swg steel body and handle fire extinguisher with textile reinforced noerane hose and high impact nozzle and strike knob. Multipurpose extinguisher rated for fire class A, B and C as manufactured by Angus Model AP 9K or approved equivallent.

name: Fire extinguisher (type:CO2)9kg all welded 16swg steel body and handle fire extinguisher with textile reinforced noerane hose and high impact nozzle and strike knob. Multipurpose extinguisher rated for fire class A, B and C as manufactured by Angus Model AP 9K or approved equivalent.

name: Hose reel 30m long, 20mm dia swinging access hose reel, including hexagonal union and gate valve for maintenance isolation of hose reel, as Angus Model 3 or approved equivalent

name: Canvas hose reel  , of 2.5” x 30m, Diffuser nozzle 2.5” Inlet, 450 Ipm@7bar (or equivalent)

name: Hydrant Cabbinet Model no NHC 900 Cabinet dimensions W=90cm H=100cm D=25cm, Height of legs 60cm from floor level, Fire hoses Nos, of 2.5” x 30m, Diffuser nozzle 2.5” Inlet, 450 Ipm@7bar (or equivalent)

name: Hydrant Cabinnet Model no NHC 900 Cabinet dimensions W=90cm H=100cm D=25cm, Height of legs 60cm from floor level, Fire hoses Nos, of 2.5” x 30m, Diffuser nozzle 2.5” Inlet, 450 Ipm@7bar (or equivalent)

name: Two way Breeching Inlet valve, hand wheel  Spheroidal Graphite Cast Iron to BSEN 1563 : 1997 in a dry riser cabinet

name: Supply, installation, testing and commissioning of the Complete Oxygen Plant with all necessary accessories

name: Supply, installation, testing and commissioning of the Chroiline Solution Plant complete with all necessary accessories

name: Supply, installation, testing and commissioning of the Osmosis Solution Plant complete with all necessary accessories

name: Provision amount for Genaral testing and commissioning

name: 350KVA Complete Generator Set, 400V. As to Netral/ Schneider Electric Manufacture or approved equivalent

name: Earth the Generator sets as per IEE regulations and code of practice, so as to achieve a final earth resistance value NOT exceeding 1.00 Ohm.

name: Allow for all civil works for the Compact sub-station Plinth

name: Cable 4x50mm2  XLPE/SWA/PVC from SUB-STATION to NPVS

name: Cable 4x25mm2  XLPE/SWA/PVC from Feeder Pillar to WWTP, PUMP HOUSE

name: Cable 4x16mm2  XLPE/SWA/PVC from Feeder Pillar to WATER TANK

name: Cable 4x4mm2  XLPE/SWA/PVC from Feeder Pillar to Consumer Units

name: Cable 35mm2  Y/G XLPE/SWA/PVC from SUB-STATION to FEEDER PILLARS

name: Cable 16mm2  XLPE/SWA/PVC from Feeder Pillar to Consumer Units

name: Cable 4x10mm2 XLPE/SWA/PVC from Feeder Pillar to Consumer Units

name: Cable trench 400mm wide x 600 - 800mm deep comprising 100mm with cable warning tapes. (Price include excavation, backfilling )(Provisional Route length might change depending EUCL source)

name: Allow a Provisional Sum of USD 15,000 to liaise with the Authorities to provide 3-phase 15kV power to the premises c/w 300m of 95mm sq HT (MV) Copper Cable and 3-phase MV metering unit & protection of the system, Including attendance.

name: 500A, 415V, (IP 65 MAIN DISTRIBUTION BOARD),  c/w Busbar couplers, MCCBS surge protection & Instrumentation as per RW-KIG-PETR-BSSS-ECOP-004 to SLD as SCHNEIDER/ Netral ELECTRIC BLOCKSET Manufacture Including a 125kvAr automatic compensation panel, or approved equivalent, as per specifications and drawing, and approved by Utility

name: Cable 3(1x50)mm2 XLPE/SWA/PVC  from REG Line to Compact Sub-station.

name: 100Watts Single arm external lighting pole complete with connection trap at 6 meter height. The price should include the concrete base and all necessary accessories.

name: 18Watts Waterproof wall light for external walls including all necessary accessories.

name: Supply and install 110 mm dia. Stainless steel FLOOR DRAIN in the wet areas floor.

name: Contruct 600x600mm Man Hole (MH) chambers in concrete complete with Cast Iron cover

name: Contruct 500x500mm Gulley Trap (GT) chambers in full concrete complete with Cast Iron cover

name: Contruct 500x500mm Control Valve Trap (CVT) chambers in full concrete complete with Cast Iron cover

name: BS-1 Booster Set (1 DUTY+1 STAND-BY+1 FREQUENCY CONTROLLED) 2x20 Cu. Meter/hour, Head: 60-90m, Capacity: 11KW.

name: BS-2 Booster Set (1 DUTY+1 STAND-BY+1 FREQUENCY CONTROLLED) 2x15 Cu. Meter/hour, Head: 60-90m, Capacity: 7.5KW.

name: BS-3 Booster Set (1 DUTY+1 STAND-BY+1 FREQUENCY CONTROLLED) 2x15 Cu. Meter/hour, Head: 60-90m, Capacity: 7.5KW.

name: FP V: 40m³/h - H: 120 mWg Complete set Fire Fighting Pump compsed by Electric, Diesel and Jocky pumps. (200Liters pressure tank, Control panel)

name: 40 CuM Underground Concrete Buffer tank complete with all necessary accessories includes: Inlet and Outlet pipes, Rudder, clearn out, etc.

name: 10 CuM Modular Plastic water tank complete with all necessary accessories includes: Inlet and Outlet pipes, clearn out, etc.

name: Complete centralized Solar Water Heater system with all necessary accessories includes; Structure suppot

name: 50PE Capacity Complete Waste water Treatment Plant including concrete works. All details as per specialist document/Details.

name: Standard SCHINDLER Model 3300AP MRL -Ex China Passenger lift or any other similar approved brand with capacity of 1000 kg 13 Passengers; with 3 stops; speed 1.0m/s; 1 door: 900mm . Complete with AVR unit, emergency drop off system, full load control and earthquake control.

name: Air hundling unit,  Supply Air 700x 700  2860 l/s 320 pa

name: Air hundling unit, Cooling Coil DX 1800 x 1200  80 KW

name: Return Fans, Fan  #1 Axial Duct Mounted 630 mm       2050 l/s  280 Pa

name: Return Fan ,Fan # 1 Axial Duct Mounted    630 mm      1710 l/s       280Pa

name: Return fan, 2 x Attenuators Per Fan       Incl 630 mm

name: Return fan, Roof Discharge – Mushroom 2   700 x 700

name: Supply  valves, Disc, Aluminium or Metal White Epoxy 200 mm    45 l/s

name: Supply valves, Disc, Aluminium or Metal White Epoxy 160 mm      20 l/s

name: Extract louvre, 4 way Aluminium or Metal White Epoxy  450x450 mm 200 l/s

name: 10mm work to walls, or concrete; trowelled to receive porcelain wall tiles.

name: Extract louvre, 4 way Aluminium or Metal White Epoxy   300*300 mm 90 l/s

name: Extract louvre, 4 way Aluminium or Metal White Epoxy 250x250 mm  50 l/s

name: Volume Control, 24 V Galvanised Sheet Metal 200 Ø 180 l/s

name: Volume Control, 24 V Galvanised Sheet Metal 160 Ø    80 l/s

name: Sensor units, Temperature / Humidity Sensor

name: Sensor  Plantroom, Temperature / Humidity Sensor

name: Supply and installation of selected 6mm thick ceramic wall tiles.,

name: Provision amount for General testing and commi'ssioning

name: 20mm. thick to receive finish; skirting with 100mm high

name: Clear site of all bushes, shrubs, small trees, undergrowth and the like generally, grub up roots and mulch on site.

name: Stripping average 250mm thick layer of top soil and cart away from site on a dumping site approved by authorities.

name: Open face excavation to form platforms under building and civil / landscaping areas and hauling and spreading materials to an approved tipping area on-site authorised by Architect in charge

name: Load, wheel and deposit surplus excavated materials off site in an area approved and/ or directed by the Local Authorities.

title: Construction works of the High Level Isolation Unit

title: Nego minutes

title: Bill of quantities_new

title: Bill of quantities_new

title: Bill of quantities_new

title: Bill of quantities_new

title: Bill of quantities_new